Unplug or disconnect the unit at the fuse box or circuit breaker before making any repairs. NOTE: We strongly recommend that any servicing be performed by a qualified professional. Frigidaire package terminal air conditioners and heat pumps provide a high...
This unit hasmanyexcitingfeatureswhich are differentfromthosefoundonstandardPTAC models.Theownermustbefamiliarwith these featuresin orderto fully understandthe operationand capabilityof the unit. • Intelligence -- Your unit has an on board computer that utilizes real time diagnostics to prolong the life of your unit. There is an LED indicator on the control board,...
ELECTRICAL SHOCK HAZARD Failure to follow this warning could result in personal injury or death and/or property damage. DO NOT alter cord or plug or use an extension cord. POWER CONNECTION OPTIONS Amperage and voltage of the PTAC and branch circuit must match according to local cord.
4.Pull out the unit from the wall sleeves. 5.Install sleeve into the wall (please see Installation Instructions of PTAC Sleeve for details). Note; We recommend always to use a Frigidaire sleeve, When units are shipped without a sleeve: In applications where unit...
WALL SLEEVE USING A NON- FRIGIDAIRE GRILLE Using a Frigidaire wall sleeve with a non-Frigidaire grille requires installation of an Accessory Baffle Kit (see Fig. 7), which ensures a good seal between the unit and exterior grille to prevent air recirculation.
INSTALLATION OF A FRIGIDAIRE PTAC INTO A FRIGIDAIRE WALL SLEEVE 1. Carefully remove shipping tape from the front panel and vent door. See Fig. 8. 2. Remove shipping screw from the vent door, if present. See Fig. 9. 3. Remove front panel. See Fig. 10.
VENTILATION CONTROL The ventilation control lever is located at left side of unit, behind the front panel. NOTE; The vent door shipping screw must be removed before using vent control lever. See Installation Instructions. When set at CLOSE, only the air inside the room is circulated and filtered.
DIP SWITCHES Auxiliary dip switch controls are located behind the front panel, through an opening below the control panel. To access, remove front panel. See Fig. 10. Dip switches are accessible without opening the Switches control box. Unit must be powered OFF to effectively change their status.
KEYPAD CONFIGURATION Keypad Configuration You can customize your unit additionally using the keypad configuration options. To enter Keypad confiquration Connect the unit to power. Press and hold the "fan speed" and the "V" for5 continuous seconds, within 30 seconds of the unit being powered up.
WALL THERMOSTAT TERMINAL IMPORTANT: Only trained, qualified personnel should access the electrical panel on unit and install electrical accessories. Please contact your local electrical contractor, dealer, or distributor assistance. Thermostat Wire Routing Thermostat wire is field supplied. Recommended wire gauge is 18 to 20 gauge solid thermostat wire.
Freeze Guard protection. See Fig. 20 and Fig. 21 for terminal connections. INTELLIGENT SELF=CHECKING CONTROL Your Frigidaire PTAC has a computer on-board that continuously checks key components of the unit to ensure they are operating properly. Under normal operation,...
temp/timer  hi  indoor  set#oint  cool reed  fanonly  b  heat auto Fig. 22 - PTAC CONTROLS ABOUT THE CONTROLS ON YOUR UNIT i."ON-OFF" : Itisused forturningON / OFF the unit. 2. "mode": Ttisused forswitchingbetween Cool,Fan and Heat mode. 3.
7. Timer function (1) Timer ON: When the unit is off, timer ON can be set. Setting range is 015_24h. When timer ON time is reached, the system will operate according to the set mode. (2) Timer OFF: When the unit is off, timer OFF can be set. Setting range is 0.5_24h. When timer OFF time is reached, the system will stop operation.
FRONT PANEL AND CASE Turn unit off and disconnect power supply. To clean, use water and a mild detergent. DO NOT use bleach or abrasives. Some commercial cleaners may damage the plastic parts. OUTDOOR COIL Coilon outdoor sideof unitshould be checked regularly. U nitwill need to be removed from its sleeve to inspectdirtbuild-upthat can occur inside of the coil.
Preventative maintenance is essential to proper unit operation, efficiency and longevity. To ensure equipment operates properly, it must be properly maintained. Equipment operation should checked and verified several times during each year. During regular unit inspection and maintenance, follow the guidelines below: .
POSSIBLE CAUSES SOLUTIONS UNIT DOES NOT START • Check that plug is plugged securely in wall receptacle. , Unit may have become unplugged Note: Plug has a test/reset button on it. Make sure that the plug , Fuse may have blown has not tripped.
SAFETY PRECAUTIONS DANGER! Avoid Serious Injury or Death 1. Do not attempt to install air conditioner by yourself. 2. This air conditioner contains no user-serviceable parts. Always call an authorized Electrolux servicer for repairs. When moving the air conditioner, always call an authorized Electrolux servicer for disconnection...
Your appliance is covered by a limited one-year warranty and a limited 2-5 year warranty on the sealed system (the compressor, condenser, evaporator and tubing). For one year from your original date of purchase, Electrolux will pay all costs for repairing or replacing any parts of this appliance that prove to be defective in materials or workmanship when such appliance is installed, used and maintained in accordance with the provided instructions.