CONTENTS —————— 1～4 WHP13300PSDPC8FQ SPECIFICATION SCOPE SPECIFICATION OF THE MODEL THE PARAMETER OF MOTOR CHARACTERISTICS PARTS AND DRAWING LIST HEAT PUMP Compressor CRITERIA ————— 5～15 ———— 16 CHECK UPON DELIVERY BASIS FOR CHECKING UPON DELIVERY RULE FOR CHECKING UPON DELIVERY DRAWINGS ——————————...
S U B J E C T M o d e l W H P 1 3 3 0 0 P S D P C 8 F Q S P E C I F I C A T I O N PAGE：1/31 SCOPE T h i s s p e c i f i c a t i o n i s a p p l i e d to SHANGHAI HIGHLY Heat pump water heater compressor.
S P E C I F I C A T I O N PAGE：2/31 *.COP= Heating capacity (W) Motor input *.Rated Capacity and input are measured with HITACHI inverter circuit by secondary Refrigerant calorimeter Methods of JIS B8606 by SHANGHAI HIGHLY Electrical Appliances Co., Ltd. Refrigerant R290 Displacement 54.8ml /rev（Double-cylinder...
S U B J E C T M o d e l W H P 1 3 3 0 0 P S D P C 8 F Q S P E C I F I C A T I O N PAGE：4/31 4.2.
H E A T P U M P W A T E R H E A T E R C O M P R E S S O R C R I T E R I A PAGE：5/31 COMPRESSOR CRITERIA 1 Strictly observe the specification The compressor should be used in specifications written in this “compressor specification”...
H E A T P U M P W A T E R H E A T E R C O M P R E S S O R C R I T E R I A 热 泵 热 水 器 专 用 压 缩 机 使 用 基 准 PAGE：6/31 There should be superheated gas returned to the compressor under all normal operating conditions.
H E A T P U M P W A T E R H E A T E R C O M P R E S S O R C R I T E R I A PAGE：7/31 raph 1 图 1 Condensing temperature 70℃...
H E A T P U M P W A T E R H E A T E R C O M P R E S S O R C R I T E R I A 热 泵 热 水 器 专 用 压 缩 机 使 用 基 准 PAGE：8/31 9 Dust of compressor hermetic terminals Compressor hermetic terminals should be mounted with specified cover in right way to prevent...
H E A T P U M P W A T E R H E A T E R C O M P R E S S O R C R I T E R I A PAGE：9/31 14 Impurities in refrigerating system （1）The weight of residue on the inside surface of the heat exchanger and tube should be less than 0.01g/m .
H E A T P U M P W A T E R H E A T E R C O M P R E S S O R C R I T E R I A 热 泵 热 水 器 专 用 压 缩 机 使 用 基 准 PAGE：10/31 18 Purge parts with dry nitrogen or dry air to remove remains in parts (dust, detergent, etc.) before assembly of system.
H E A T P U M P W A T E R H E A T E R C O M P R E S S O R C R I T E R I A PAGE：11/31 Moving tubes to the moving parts; minimum clearance 12.7mm(1/2”) Moving tubes to non-moving parts;...
H E A T P U M P W A T E R H E A T E R C O M P R E S S O R C R I T E R I A PAGE：12/31 （6）The compressor can’t be used in the place with corrosive atmosphere such as hot spring and chemical warehouse.
H E A T P U M P W A T E R H E A T E R C O M P R E S S O R C R I T E R I A PAGE：13/31 (14) SHEC will not take any responsibility against accident that is caused by the accessories equipped by yourselves.
H E A T P U M P W A T E R H E A T E R C O M P R E S S O R C R I T E R I A PAGE：14/31 It is necessary to install a dryer to dehumidify the residual moisture mixed in the refrigerant in the cycling system.
H E A T P U M P W A T E R H E A T E R C O M P R E S S O R C R I T E R I A PAGE：15/31 （27）The fuse or/and breaker should be equipped in the main circuit. (28) The thickness of the refrigerating system using tube the tube thickness as followed External diameter(mm)
C h e c k u p o n D e l i v e r y PAGE：16/31 1. Basis for Checking upon Delivery The Performance test will be carried out in accordance with this “compressor Specification”. The Safety Performance in accordance with GB4706.1 Safety of household and similar electrical appliances General requirements and GB 4706.17 Safety of household and similar electrical appliances Particular requirements for motor-compressor.
Instructions： The pressure ratio(Pcr) should satisfy the following conditions: 1）900~2000rpm：1.5≤Pcr≤8.0 2）2000~6600rpm：2.0≤Pcr≤8.0 If the suction pressure, pressure ratio out of the used envelop under normal operating conditions ， the following tips should be considered to make the compressor operating reliability. Condit Condit Condit Condition 1...
Anwendungshinweise für DC Inverter Kompressoren zur Drehzahlregelung Instruction for DC inverter compressor rotation speed control Drehzahländerung / <= Speed change rate: 133min-1/s Max und Min Drehzahl in den einzelnen Spezifikationen Max and min speed is showed in the specification Vom Start zur gewünschten Drehzahl / From starting to normal running Rotation speed Drehzahl...