3 - 18.4 - 7 ® Dual fuel burners - OXY-THERM - 5/13 Intended service and typical application Application details ® OXY-THERM FHR burners can be used in furnaces and melters, steel reheat furnaces, linear hearth furnaces, rotary hearth furnaces, reverberatory furnaces, and other high temperature applications. ®...
3 - 18.4 - 8 ® Dual fuel burners - OXY-THERM - 5/13 Ratio control requirements Correct fuel/oxygen ratio control valves should be selected. Trims should be selected to enable use with oxygen. For accurate ratio ® control, MAXON SMARTLINK MRV valves are recommended.
3 - 18.4 - 9 ® Dual fuel burners - OXY-THERM - 5/13 Flame length - gas burners Flame lengths shown are typical for burners sized and operating at maximum design conditions. Flame lengths per unit of heat input will vary from these values when burners are operated below maximum design. w w w .
3 - 18.4 - 12 ® Dual fuel burners - OXY-THERM - 5/13 Installation instructions Please read the operating and mounting instructions before using the equipment. Install the equipment in compliance with the prevailing regulations. Bedrijfs- en montagehandleiding voor gebruik goed lezen! Apparaat moet volgens de geldende voorschriften worden geïnstalleerd.
3 - 18.4 - 13 ® Dual fuel burners - OXY-THERM - 5/13 Typical burner mounting arrangement 1) Furnace wall 2) Melter wall 3) By others 4) Piping support by others Alternate burner mounting arrangement 1) By others w w w . m a x o n c o r p . c o m combustion systems for industry Maxon reserves the right to alter specifications and data without prior notice.
3 - 18.4 - 14 ® Dual fuel burners - OXY-THERM - 5/13 Burners should not be installed in a down-fired position. The primary objective is to seal the burner block in the wall of the furnace and support the weight of any system piping. The burner block sits on the sill or wall.
3 - 18.4 - 15 ® Dual fuel burners - OXY-THERM - 5/13 If fuel insert is shipped inside burner housing, remove the fuel insert and set aside in a protected area. Install service plate over housing flange and secure plate to housing using T-bolts provided. ...
3 - 18.4 - 16 ® Dual fuel burners - OXY-THERM - 5/13 Operating instructions Instructions provided by the company or individual responsible for the manufacture and/or overall installa- tion of a complete system incorporating MAXON burners take precedence over the installation and operat- ing instructions provided by MAXON.
3 - 18.4 - 17 ® Dual fuel burners - OXY-THERM - 5/13 Maintenance instructions ® The OXY-THERM FHR burner is provided with quick release clamps to allow for rapid change-over between gas and oil firing. Customer-specific procedures for shut down and blocking of fuel gas and oxygen supply to the burner must be developed and adhered to prior to attempting removal and changing of fuel inserts.