Touch Screen Controller Model Name: TCB-TSC640-PY Thank you for purchasing this TOSHIBA Carrier UK Ltd. TCB-TSC640-PY Touch Screen Controller. Please read this manual carefully before using to ensure the correct setup and operation of the TCB- TSC640-PY and related equipment.
The product was handled or used under conditions/environments that are not specified in this manual. The failure was caused by other causes than this product. The product was altered or repaired by anyone other than Toshiba Carrier UK Ltd. The product was not used in accordance with its original purpose. ...
Do not use the input functions of the touch switch, etc. of the TCB-TSC640-PY unit, in applications that involve human life, in applications that may result in serious injury, or for emergency stop switches.
Owners Manual Touch Screen Controller Do not let metal particles enter the unit’s when preparing the panel. Do not connect an AC power supply to the DC power terminals. Use a DC power with a small voltage fluctuation and that will provide a stable output even if the output is momentarily interrupted for 10ms.
Owners Manual Touch Screen Controller Introduction Application/Functions/Specifications Application The Touch Screen Controller can connect up to 64 Units/Groups up to 16 Refrigerant Circuits via the PY Interface TCUK IFMB641-0-OTR) The Touch Screen Controller can control external equipment via the TCB-IFCG1TLE General Purpose I/F. ...
Owners Manual Touch Screen Controller External View TCUK-IFMB641-0-OTR – PY Interface Mounting Holes Part Name Specification Case Galvanized sheet metal Case Lid Galvanized sheet metal Grommet C30-SG20A Grommet C30-SG20A Grommet for Power Supply C30-SG20A 6 (EN)
Owners Manual Touch Screen Controller Main Functions Application / Home Screen Schedule window, Fire alarm indication and fault Control screen. Single weekly or daily schedule alarms will be shown in the unit, Group & Zone up to 12 events per day. two boxes circled.
Owners Manual Touch Screen Controller Commissioning When commissioning the TCB-TSC640-PY touch screen controller you can use the quick start method, or please refer to section 5. Setup. This commissioning method is used when more advanced building control is required. Quick Start The quick start commissioning option reduces the amount of time required to commissions the TCB-TSC640- PY Touch screen.
Owners Manual Touch Screen Controller 2. Set date and time under the correct tab. If used/enabled also set the first and last day of Summertime. 3. In the Settings tab select Administrator . 10 (EN)
Owners Manual Touch Screen Controller 4. Select Autoscan Network Once the Autoscan has been initiated it will scan the whole TCC link for connected Indoor units. The Indoor units that are found will be automatically addressed. Please note that when completing an auto-scan it will clear all existing addressing information.
OK on pop up box displayed. (Please note the Autoscan only detects units on gateways 1 & 2. If more gateways are used please refer to section 5. Setup for remaining gateways. Note: Only one gateway is supplied with the TCB-TSC640-PY The Quick Start method is now complete.
Owners Manual Touch Screen Controller Setup Settings Settings Overview - The settings tab is used for a number of different features. These features are as follows. Time & Date – This tab allows you to set the current date and time. It is also where you set up the first and last day of Summertime for schedule operations.
Owners Manual Touch Screen Controller Name, Zones & Hierarchy The Name Zones & Hierarchy tab is used to create level names and zones. As shown in the image below you have up to 3 levels of control. The Unit Config Screen & hierarchy is used for the advanced setup procedure.
Owners Manual Touch Screen Controller To begin the commissioning first selects the type of unit. To do this, please press the section box in type column. This will take you to the screen showed below. You have the option to select from VRF type indoor units and LC indoor units.
Owners Manual Touch Screen Controller In the top left corner of the customise (indoor unit setup – Limits) screen you can press a blue arrow take you to the next customise screen. In this screen you can apply restrictions to what functions an indoor unit can control.
Owners Manual Touch Screen Controller In the Names Zones and Hierarchy tab there is also a Hierarchy select button. Once you have selected this button you will see the screen below. This screen is where you apply indoor units to the levels you have created.
Owners Manual Touch Screen Controller GPIF Interlocks – Only applicable if at least 1 General Purpose Interface is installed. The purpose of the General Purpose Interface interlocks is for using inputs to trigger outputs such as External Lighting, Ventilation, Air Quality Sensor and Occupancy Control without the need of an external controller. Once you have pressed the GPIF interlock tab the screen below will be displayed.
Owners Manual Touch Screen Controller This Screen in the GPIF interlocks tab is the Interlock write setup for indoor units. You have the same level as control as the master control screen. The Screen below is the interlock write setup for Digital and analogue outputs. 19 (EN)
Beep on key press. As standard the beep on key press will be on from factory you can enable or disable the feature using this selection box on the touch screen. The languages that are available for the TCB-TSC640-PY Touch screen are as follows: ...
Owners Manual Touch Screen Controller Administrator – The administrator tab will allow you to do the following, Autoscan network, create passwords, factory reset, erase alarm history, display auto mode, Firestop enable/ Firestop invert input signal/ Firestop auto- restart. Firestop enable – Please select Firestop enable if fire alarm input is being used. Once selected a green tick will appear in the selection box.
Owners Manual Touch Screen Controller Autoscan The Autoscan will find all connected indoor units and as standard will scan for two PY gateways. If more than two PY gateways are being used you will need to manually enter the addressing information for the additional gateways.
Owners Manual Touch Screen Controller The Autoscan may not detect all connected indoor units. In particular new series indoor units and indoor units with service PCB’s could be missed. Please enter these indoor units using the manual addressing procedure as explained from page 14-16. Passwords ...
Owners Manual Touch Screen Controller Factory Reset In the administrator tab there is an option to reset the touch screen to factory settings. This will clear all addressing information and all information you have entered to the settings tab. The screen below is to show the warning message that will appear once the factory rest has been selected.
Owners Manual Touch Screen Controller Settings page 3: Clear GPIF interlock settings Settings page 4: Language setting = ENGLISH Temperature units = °C Temperature steps = 1° Temperature limits = 18.0°C to 29.0°C Screen saver time = 10 minutes ...
Owners Manual Touch Screen Controller Operation Control Direct & Master control screens Once you have selected the control screen via the home button, the master control screen is displayed. The quick control screen has the following features. Master control screen The master control screen allows you to set the power status, mode status, fan status, temp status, louvre status and filter reset.
Owners Manual Touch Screen Controller Direct control screen Levels & Zones Levels & Zones that you have created in the administrator menu can be filtered using the arrows on the left hand side of the single and multiple unit control screen. Use the icon to switch between level and zone control. ...
Owners Manual Touch Screen Controller Mode The mode can be changed via the direct control screen. If you are using a 3 pipe system you will need to select the auto mode option in the settings - Administrator screen. Mode options that can be set are Auto (If enabled) Heat, Cool, Dry, and Fan only ...
Owners Manual Touch Screen Controller 6.2 Schedule Schedule overview In the schedule tab, you can create up to 32 individual schedules. Each schedule can have up to 12 operations per day. This screen is displayed when schedule is selected from the Home Screen. From this screen you can access the schedule configuration screen by selecting one of the 32 Schedules.
Owners Manual Touch Screen Controller Schedule Configuration 1. Name In the schedule configuration screen you can enter a name for the schedule you are creating. This name will then be displayed in the schedule overview screen as shown on page 38. 2.
Owners Manual Touch Screen Controller 6.3 Overview The Building overview screen shows the status of the indoor units. (Some level of control is available using the global control commands) When the overview button is pressed on the home screen, it will take you to the screen displayed below.
Owners Manual Touch Screen Controller Detailed Building overview The detailed building overview screen is to show the status of indoor units. Quick control function is not available. To change the Fan speed etc., please select Icon number 4. below, this will take you to the control screen.
Owners Manual Touch Screen Controller Faults Faults Overview – In the faults tab, there are two separate screens. Screen 1 is for active alarms and screen 2 is for the alarm history. Active Alarms The active alarm screen is shown below. This screen will display all active alarms and the data and time that the alarm was raised.
Owners Manual Touch Screen Controller Alarm History All alarms are displayed in the Alarm History screen. The Alarm history will display the last 2000 alarms. When the Alarm History log is full it will begin to overwrite the oldest alarms. The Alarm History screen will display the date and time that an alarm occurs and the data and time that it is cleared.
Owners Manual Touch Screen Controller Maintenance –Touch Screen Controller BEFORE starting Touch Screen Trial Operation This section describes the inspection and cleaning method of the touch screen. Please clean and check the touch screen periodically to ensure the touch screen is always in the best optimal condition.
Alarm History List. To ensure correct communication, verify that no error exists in the Active Alarm or Alarm History list of the controller. TOSHIBA CARRIER UK LIMITED PORSHAM CLOSE, BELLIVER IND EST, PLYMOUTH, UK, PL6 7DB PRODUCT OF PLYMOUTH ENGINEERING DEPARTMENT...