The AEW310.2 pulse adapter acquires and handles the pulses from 1 or 2 con-
sumption meters with pulse output and transmits the data to an M-Bus-network.
For setting the parameters, the pulse adapter can be programmed via M-Bus
interface before connecting to the network.
The pulse adapter is a component of the M-Bus system. It is used when data of pulse
output meters shall be collected by a M-bus system. Such devices can be meters for
hot water, cold water, gas, electricity, etc.
Acquisition of the pulses delivered by the connected consumption meters
Monitoring the connecting cable in the case of metering devices with NAMUR circuit
Handling of pulses and storage of consumption data and set day values
Transmission of data telegrams on demand to the M-bus master