Pulse Adapter AEW310.2 The AEW310.2 pulse adapter acquires and handles the pulses from 1 or 2 con- sumption meters with pulse output and transmits the data to an M-Bus-network. For setting the parameters, the pulse adapter can be programmed via M-Bus interface before connecting to the network.
Connection of 2 meters to the connecting cable by means of the cable connectors sup- plied with the unit. Ordering When ordering, please give type reference: AEW310.2 Equipment combinations When installing, the pulse adapter must be programmed with the data set delivered with the parameter setting software for the respective meter.
Then, squeeze the connector with a pair of pliers. This connection cannot be separated and offers degree of protection IP54. Only for AEW310.2/DK: With the housing cover open, insert the meter connecting cables with the O-ring from the rear of the unit into the cable strain relief and connect the cables to the terminal block.
Perm. ambient temperature Transport and storage 25…+60 °C Operation 0…55 °C Weight 0.3 kg The documents can be downloaded from http://siemens.com/bt/download. Connection diagrams Connection of any type of meters with pulse output INP 1 INP2 AEW310.2 pulse adapter P1, P2 Meter with pulse output...
Dimensions 27,3 95,5 Dimensions in mm Connecting cable length is 350 mm. Building Technologies Pulse Adaptor AEW310.2 CE1N5383en HVAC Products 14.12.2007 2016-02-12...