Air Conditioning Control System (Touch Screen Controller)
3-1-2. When Installing from the Rear
Main unit box
Air conditioning control system to wall, etc.
fixing hole dimensions
4-Ø4.5 round hole
* Although the panel and the main unit box are separated to explain the screw attachment part in an easy to understand
manner, it is not necessary to remove the main unit box from the panel in actual installation work.
Drill four Ø4 holes in the switchboard, wall, etc.
Fit the main unit on the switch board, wall, etc.
Fix from the rear of the main unit. Please use the supplied M3 × 8 screws.
Connect the TCC-LINK cable, AC adapter, and LAN cable to the main unit.
When installation is completed, peel off the transparent film.
Hole dimensions to drill in wall