Siemens. Trademarks All designations marked with ® are registered trademarks of Siemens AG. Other designations in this documentation might be trade- marks which, if used by third parties for their purposes, might infringe upon the rights of the proprietors.
Operating Instructions SIPLUS CMS4000 Wiring Table of Contents Preface..........................4 Purpose of this document ..................4 Required basic knowledge ..................4 Validity of this document ..................4 Modification compared with the previous version ............4 CE marking ......................4 Standards ......................4 Position in information environment ................4 Directory ........................5...
Position in information environment In addition to this operating instructions you need the manual of the applied ION and IFN hardware. SIPLUS CMS4000 IFN AI, IFN VIB-A, ION PROFIBUS DP Spy T001, MCN11 and RPN IEEE1394. SIPLUS CMS4000 Cable Operating Instructions, 06/2017, A5E02298098B-01...
Operating Instructions SIPLUS CMS4000 Wiring Directory This operating instructions consist of chapters for guidance and of technical data. They contain the following topics: · Product overview (Chapter 2) · Typical configurations (Chapter 3) · Cable types (Chapter 4) · Connecting the cable (Chapter 5) ·...
Operating Instructions SIPLUS CMS4000 Wiring Product Overview What is SIPLUS CMS? SIPLUS CMS is an industrial-suited Condition Monitoring System for technical and tech- nological services in industrial plants. SIPLUS CMS is a modular, scalable analysis and diagnosis system. It is optimized for reaction less measurement of analog, binary and numerical data.
Operating Instructions SIPLUS CMS4000 Wiring What is an Interface Node ION or IFN? Definition With an ION or IFN binary, analog or vibration signals are measured and transfered via bus system to an industry PC according to the EEE1394a Standard.
Operating Instructions SIPLUS CMS4000 Wiring Typical Configurations Tree topology The IEEE1394a technology allows to create extended networks with up to 63 partici- pants. The attendance of one branch must not be more than 16 devices. The tree-topology allows the construction of a network system by connecting one bus participant with two further ones.
Operating Instructions SIPLUS CMS4000 Wiring Interface Node (IFN) IFN/IFN-Cable IFN/IFN-Cable Picture 5 Line topology with IFN Connection with fibre optic cable The MCN11 can be connected to any IEEE1394 – connection (LNK0/1/2) on the IFN. In accordance to the minimum distance up to three MCN11 can operate at the same time.
Operating Instructions SIPLUS CMS4000 Wiring PC / SIPLUS CMS Microbox Multi-Port-Repeater (RPN IEEE1394B T001/T002) RPN/PC-Cable Media Converter Node (MCN11) Interface Node (IFN) IFN/MCN-Cable Picture 7 Optical connection of a PC on a CMS4000 System SIPLUS CMS4000 Cable Operating Instructions, 06/2017, A5E02298098B-01...
Operating Instructions SIPLUS CMS4000 Wiring Cable Types Overview The following chart gives a survey about all cables and their usage combined with ION, IFN, MCN und RPN: Name Chapter Identifier CABLE-IEEE1394A-66/46 2AA00 CABLE-IEEE1394A-8F 2AB20-1 CABLE-IEEE1394A-8M 2AB20-2 CABLE-Power 2AB30 IFN ADD...
Operating Instructions SIPLUS CMS4000 Wiring CABLE-Power Name: CABLE-Power Application: Power cable Length: 135cm, 200cm, 500cm, 1000cm Order numbers: CABLE-Power-135-0000 (135 cm) 6AT8000-2AB30-1AA1 CABLE-Power-200-0000 (200 cm) 6AT8000-2AB30-1AA2 CABLE-Power-500-0000 (500 cm) 6AT8000-2AB30-1AA5 CABLE-Power-1000-0000 (1000 cm) 6AT8000-2AB30-1AB0 Picture 12 CABLE-Power This cable is used for energy supply of the IFN. To forward the power from the first IFN to the following ones in a line topology IFN ADD must be applied, see.
Operating Instructions SIPLUS CMS4000 Wiring Chart 1: Pin assignment PWR Assignment Wire color View M24 (ground) brown +24 V DC (18…32 V DC) white blue (power down, ext. restart) free black free grey or green/yellow IFN ADD A cable set consists of one power cable with Y-plug for straight power forwarding to a neighbour IFN and one IEEE1394A coupling cable.
Operating Instructions SIPLUS CMS4000 Wiring Warning The IFN ADD power cable with Y-plug is designed for max. current load of 4 A . Maximum 16 IFNs are allowed to be connected in a line. Notice CABLE-Power-xxx-0000 (6AT8000-2AB30-1Axx) and CABLE-IEEE1394A-88-0020 (6AT8000- 2AB20-2AD2) must be applied to obtain protection class IP67.
Operating Instructions SIPLUS CMS4000 Wiring CABLE-IO Name: CABLE-IO Application: Input/Output-cable IFN-sensor Length:: 200cm, 500cm, 1000cm Order numbers: CABLE-IO-200-0000 (200 cm) 6AT8000-2AB40-1AA2 CABLE-IO-500-0000 (500 cm) 6AT8000-2AB40-1AA5 CABLE-IO-1000-0000 (1000 cm) 6AT8000-2AB40-1AB0 Picture 16 CABLE-IO This cable allows connecting the sensor technology to the IFN. The cable can be used for IFNA AI and IFN VIB-A.
Operating Instructions SIPLUS CMS4000 Wiring The following chart shows the assignment of the IEPE inputs (CH1 - CH6) using an IFN VIB-A. Chart 4 Pin assignment IEPE sensor input (CH1-CH6) Assignment Wire color View GND (ground) brown free white signal...
Operating Instructions SIPLUS CMS4000 Wiring Accessories Mounting brackets for wall mounting are available for IFN - IFN Mounting Set (6AT8000- 2BB00-0XB0) and for MCN11 - MCN Mounting Set (MLFB 6AT8000-2BB00-0XC0). Unused jacks can be closed by a capping set, IFN Coping Set (MLFB 6AT8000-2BB00- 0XA0).
Operating Instructions SIPLUS CMS4000 Wiring Connecting Cable Connect M12-plug Caution The following pictures (picture 17, picture 18 , picture 19) shall explain the principle of connecting the cable and may contain deviations from the used plug types. 1. Push the M12 connector vertical in the respective flange sleeve, so that connector slot and the knurled ring nut lie on top of each other.
Operating Instructions SIPLUS CMS4000 Wiring Picture 19 lock the plug 3. The end position (interlock) of the M12-socket plug is finished now. Picture 20 correctly plugged in Caution Avoid canting between M12 connector and socket plug! Only when the installation is correct, the protection category IP67 and safe contacting is guaranteed.
Operating Instructions SIPLUS CMS4000 Wiring Fibre optic cable connection 5.2.1 MCN11 fibre optic cable (LWL) 1. Open the 4 screws on the device with an Allen key (SW3). Picture 21 Open all 4 screws 2. Release only the screwcap of the screw connection (PG-screwing) and pull the „SC/PC plug“...
Operating Instructions SIPLUS CMS4000 Wiring 4. Insert the SC/PC-plug of the LWL cable strands through the cable entry into the housing. Case screw (4x) Sealing insert Screwcap SC/PC-plug Cable entry Picture 23 LWL-cable entry configuration 5. Connecting „SC/PC-plugs“. Device 1 Device 2 ▼▲...
Operating Instructions SIPLUS CMS4000 Wiring 6. Slide the sealing insert flush in the cable entry so that the LWL-single connector lays parallel in the box (in order to avoid a mechanical overload of LWL). 7. Screw the retainer nut tightly onto the cable entry. The recommended torsional mo- ment is 10Nm.
Operating Instructions SIPLUS CMS4000 Wiring 5.2.2 RPN IEEE1394A fibre optic cable (LWL) According to its design the RPN has one or two duplex SC/PC62.5 fibre optic cable adapter. LWL adapter ground IEEE1394 adapter (LNK) LWL adapter power supply Picture 26 RPN IEEE1394B T002 Interface...
Operating Instructions SIPLUS CMS4000 Wiring Appendix Service & Support in the Internet In addition to our documentation pool we offer our complete knowledge basics on the In- ternet: www.siemens.com/automation/service&support There you find: • The newsletter, which is constantly updated to provide you with the latest information about your products.