The MMI Port is a 9-pin port of the front of the PLC. This is the method tested for this manual. This is a one-to-one Link (one PLC per com port). This Guide was tested using a 9-pin to 9-pin cable labeled JW10/TP02 PC. The Sharp User’s Manual describes a cable from Sharp (model JW-12KC). This is a 9 pin to 25-pin cable.
Transfer Rate = 19200 188.8.131.52 2-wire Communications Port The JW10 has a two-wire Communications port for using the computer link, data link or remote IO. This function is determined by system memory #234: #234 = 0 = Computer Link Mode (required by WebAccess) #234 = 1 = Data Link #234 = 2 = Remote I/O Link.
WebAccess and will overwrite any write from WebAccess. Note 2 – The PLC must be in RUN mode for physical IO to be scanned by the PLC and written to memory of PLC. 3. Configure a Sharp JW device Summary 1.
Advantech WebAccess Device Driver Guide Sharp JW 10 Serial Comport. 7. Configure Baud Rate, Data Bit, Stop Bits and Parity to match those in the PLC. All PLCs on this Comport must use the same settings. The default settings (memory #236 or #226 = 00000000) are:...
Advantech WebAccess Device Driver Guide Sharp JW 10 Serial Figure 3.1 Serial Comport properties for Sharp JW – MMI Port, default settings (Memory #236 or #226 = 00000000 3.2.1 Comport Number The Serial Comport requires the comport number to match that of the physical interface (e.g.
8 bits. 3.2.5 Stop Bits For the Sharp JW 10 there can be 1 or 2 Stop Bits. The default setting is 1 stop bit. This must match the number of stop bits configured in the PLC. Please refer to the Manufacturer’s Documentation to determine the actual number of Stop...
3.2.10 Auto Recover Time The Sharp JW 10 was tested with Auto Recover Time = 60 Seconds. Auto Recover Time is the time to wait before attempting to re-establish communications with a BAD device or port.
User assigned description up to 70 characters 3.3.3 Unit Number Unit Number, for Sharp JW, must correspond to the Unit Number used in the protocol addressing. If using the MMI Port, since only one-to-one communications is supported via the MMI port, the PLC address is 1.
3. Start WebAccess Configuration. 4. Select Project. 5. Select SCADA Node. 6. Select the Sharp JW10 Device. 7. Select Add Tag. 8. From Parameter Pull Down List Select Reg0. This will configure an Analog Input. Wait for the Page to update.
14. Press Submit. Digital Tag This example is to configure a Tag that writes a Digital Output (Address DO 15. Select the Sharp JW10 Device. 16. Select Add Tag. 17. From Parameter Pull Down List Select DO. This will configure an Analog Input.
Advantech WebAccess Device Driver Guide Sharp JW 10 Serial 22. Optionally enter, State 0 Description, State 1 Description, Alarms, enable data logging, etc. 23. Press Submit. Congratulations! You have just configured a Measurement and Output Tags to Sharp device. Version 6.0 rev 0 Advantech Corp., Ltd.