Arrange the connection wire using the supplied
cable ties so that, when the cover-back is back in
place, it is located under the cover-back.
Lower down the cover-back so that it is in place.
Connect the connection wire to the indoor unit PBA.
When connecting the wire to the indoor unit PBA,
check the colors and numbers of the pins on the
MDS Kit error indication
(displayed on the indoor unit)
If you turn off the air conditioner when an LED is flickering, the LED is also turned off.
Assemble the panel onto the indoor unit.
For more information about assembling the panel,
refer to the Panel installation manual.
Set the MDS Kit installation option using the wired
or wireless remote control.
Because the indoor unit ships with the MDS Kit
installation options set to "Disuse", you must change
the value of the MDS Kit installation option.
For more information about how to set the MDS
Kit installation options, see Setting the MDS Kit
installation option on page 7 and the indoor unit
Enter the installation option value more than twice.
After entering the installation option value, reset the
indoor unit to check for correct operation.
LED lamp display