Operation and Installation Instructions
Alarm Extender Module
The SIEMENS Model AE-30U Alarm Extender
Module is designed to provide one Style Y (Class
B) super-vised notification appliance circuit,
utilizing polarized, parallel connected notification
appliances. Actuation of the module is caused by
high-going DC input signal between 12 and 24 volts
above system common. Dual input activation termi-
nals are provided to facilitate programming.
The Model AE-30U contains a yellow LED trouble
indicator to display open or shorted alarm lines
except when that particular module is not in an
The yellow LED can be lamp tested from the
system control panel.
1. Mount the module to the horizontal mounting
brackets in the control enclosure.
2. Install the Model JA-5 (5 in. long) bus connector
cable assembly between receptacle P2 of the
module and receptacle P1 of the module or
control panel immediately preceding it in the
Note: If the preceding module is on another
row in the enclosure, a JA-24 (24 in.
long) bus connector cable assembly will
3. Modules are to be bus-connected from right to
left. For two-row enclosures, the modules in the
lower row are to be connected from left to right.
Succeeding rows are to be alternately con-
nected, right to left, left to right, etc.
4. If a module is the last module in the system,
install either a JS-30 (30 in. long) or JS-64
(64 in. long) bus connector assembly from the
Siemens Building Technologies, Inc.
8 Fernwood Road
Florham Park, New Jersey 07932
unused receptacle of the last module to
terminal 41 of the CP-35 control panel. This
completes the module supervision circuit.
5. If a DC notification appliance circuit is to be
used, install a JP-D program plug into
receptacle P2 of the CP-35 control panel.
Note: If a battery charger/transfer module is
used, the program plug is not
If an AC notification appliance circuit is to
be used, install a JP-A program plug into
receptacle P2 of the control panel.
Note: When a JP-A program plug is used, an
EL-32 end of line device is required for
the notification appliance circuit.
6. Wire the circuits as described in the MODEL
CP-35 CONTROL PANEL INSTALLATION
AND MAINTENANCE INSTRUCTIONS, P/N
315-085063 and the CP-35 WIRING DIAGRAM,
P/N 315-084902. The maximum line resistance
should be 3 ohms, and a minimum of 14 AWG
wire is recommended. All wiring should comply
with the local and national codes that apply to
the particular installation.
Refer to INSTALLATION AND WIRING in the
Instruction Manual (P/N 315-085063) for the
Refer to TROUBLESHOOTING THE CP-35 in the
Instruction Manual for the control panel.
Siemens Building Technologies, Ltd.
2 Kenview Boulevard
Brampton, Ontario L6T 5E4 CN