Precautions for Installing the Q Series Large Type Base
Unit (AnS Series Size)
(1) Module installation position
Provide the following distances between the top and bottom of the
module and other structure or components to ensure ventilation for
heat dissipation and to change the module easily.
5mm or more *2, *6
*1 30mm or more is required when writing duct is 50mm or less in height. Otherwise, at least
40mm is required.
*2 20mm or more is required when the extension cable is connected without removing
*3 80mm or more is required when the connector type is used. For Q8BAT, 80mm or more is
required when the connection cable for Q8BAT is used.
*4 For Q7BAT, 45mm or more is required.
*5 For Q8BAT, 30mm or more is required from both top and bottom sides of the module.
*6 For Q8BAT, 5mm or more is required from both left and right sides of the module.
(2) Module installation direction
(a) Install the programmable controller in the direction shown
Indicates the control panel top,
wiring duct, or any part position.
below to ensure ventilation for heat dissipation.
5mm or more *6