Junction box not
* Tamper Output. When activated, output syncs to ground (default).
** Dependent upon reader configuration. See HTOG Wiegand and Clock-and-Data configurations for more
*** For 5 meter pigtail readers, PN: 9xxxxxLEKxxxxx follow the wiring diagram on the reader.
Open Collector Output - Controls an external device (5 VDC) operating in Host Mode only. Sink – 40mA / Source – 1mA.
Configuration Cards – With the use of configuration cards, the reader can be modified to meet the specific requirements of an installation. Configuration options include; audio
visual, CSN outputs and keypad outputs (keypad models only). Contact HID Technical Support for all reader configuration options.
Hold Input – when asserted, this line either buffers a card or disables a card read until released, as configured.
R10E/RP10E/R10MA/RP10MA, R15E/RP15E/R15MA/RP15MA, R40E/RP40E/R40MA/RP40MA, RK40E/RPK40E/RK40MA/RPK40MA
Observe precautions for handling
ELECTROSTATIC SENSITIVE DEVICES
LED Input (GRN)
LED Input (RED)
*Open Collector Output/Tamper
**Wiegand Data 1 / Clock
**Wiegand Data 0 / Data
Install Reader to Backplate
Power & Testing
Turn on power
Note: Previous OmniClass readers had reversed RS-485 wiring (P2-7 & P2-6 - A
& B). When upgrading to an OmniClass SE reader, ensure proper connections as
Note: It's possible to reuse existing Wiegand wiring for OSDP, however, using simple
stranded cable typical of Wiegand access control readers is usually not meeting the
RS485 twisted pair recommendations.
Note: For OSDP cable lengths greater than 200ft. (61M) or EMF interference, install
120Ω +/- 2Ω resistor across RS-485 termination ends.
Note: Wiring the reader incorrectly may permanently damage the reader.
Note: With a keypad reader, operating as 26 bit emulation; upon power up you have
5 seconds to enter the facility code followed by #. If unsuccessful, the reader LED
displays solid Red. Power-cycle the reader and retry entering the facility code.
The facility code needs to be manually entered as 3 digits (i.e. if facility code is 10
enter 0-1-0-#). Note: OmniClass 2.0 readers only use facility codes between 1-255,
and there is no default facility code. Once the facility code has been entered, the LED
will display Violet and then to a final Red. Then power-cycle the reader. Note: When
using a keypad, if there are 2 short beeps after entering your PIN, the reader does
not have a facility code configured yet. In this event, an Admin will need to be power-
cycle the reader and enter the facility code before the reader will accept your PIN.
OM15/16/17/18, OM30/31/32/33, OM40/41/42/43, OM55/56/57/58
PLT-01558, Rev A.1