3. Service integrated control module or connecting wiring following the discharge process in step 2. Use caution not to recharge
your body with static electricity; (i.e., do not move or shuffle your feet, do not touch ungrounded objects, etc.). If you come
in contact with an ungrounded object, repeat step 2 before touching control or wires.
4. Discharge your body to ground before removing a new control from its container. Follow steps 1 through 3 if installing the
control on a furnace. Return any old or new controls to their containers before touching any ungrounded object.
Before installing this unit, please read this manual thoroughly to
familiarize yourself with specific items which must be adhered to,
including but not limited to: unit maximum external static pres-
sure, gas pressures, BTU input rating, proper electrical connec-
tions, circulating air temperature rise, minimum or maximum CFM,
and motor speed connections.
This furnace is primarily designed for residential home-heating applications. It is NOT designed or certified for use in mobile homes,
trailers or recreational vehicles. Neither is it designed or certified for outdoor applications. The furnace must be installed indoors
(i.e., attic space, crawl space, or garage area provided the garage area is enclosed with an operating door).
This furnace can be used in the following non-industrial commercial applications:
Schools, Office buildings, Churches, Retail stores, Nursing homes, Hotels/motels, Common or office areas
In such applications, the furnace must be installed with the following stipulations:
It must be installed per the installation instructions provided and per local and national codes.
It must be installed indoors in a building constructed on site.
It must be part of a ducted system and not used in a free air delivery application.
It must not be used as a "make-up" air unit.
It must be installed as a two-pipe systems for combustion air.
All other warranty exclusions and restrictions apply This furnace is an ETL dual-certified appliance and is appropriate for use
with natural or propane gas (NOTE: If using propane, a propane conversion kit is required).
Dual certification means that the combustion air inlet pipe is optional and the furnace can be vented as a:
Non-direct vent (single pipe) central forced air furnace in which combustion air is taken from the installation area or from
air ducted from the outside or,
Direct vent (dual pipe) central forced air furnace in which all combustion air supplied directly to the furnace burners through
a special air intake system outlined in these instructions.
This furnace may be used as a construction site heater ONLY if all of the following conditions are met:
The vent system is permanently installed per these installation instructions.
A room thermostat is used to control the furnace. Fixed jumpers that provide continuous heating CANNOT be used and can
cause long term equipment damage.
Return air ducts are provided and sealed to the furnace.
A return air temperature range between 60ºF (16ºC) and 80ºF (27ºC) is maintained.
Air filters are installed in the system and maintained during construction replaced as appropriate during construction, and
upon completion of construction.
The input rate and temperature rise are set per the furnace rating plate.
100% outside air is provided for combustion air requirements during construction. Temporary ducting can be used.
NOTE: Do not connect the temporary duct directly to the furnace. The duct must be sized for adequate combustion and
ventilation in accordance with the latest edition of the National Fuel Gas Code NFPA 54/ANSI Z223.1 or CAN/CSA B149.1
The furnace heat exchanger, components, duct system, air filters and evaporator coils are thoroughly cleaned following final
construction clean up.
All furnace operating conditions (including ignition, input rate, temperature rise and venting) are verified according to
these installation instructions.
NOTE: The Commonwealth of Massachusetts requires that the following additional requirements must also be met:
Gas furnaces must be installed by a licensed plumber or gas fitter.
O PREVENT PROPERTY DAMAGE
DO NOT INSTALL THIS FURNACE IN A MOBILE HOME
PERSONAL INJURY OR DEATH DUE TO