Caution! Gas water heater must be installed in a location out of bathroom where well ventilated. Its
prohibited to install natural discharge type gas water heater in a room with a poor ventilation condition. User
should apply for local gas administrative institution approval before installation. and the installation must also
be approved by local civil administrative department, installation should only carried out by the Service center
which are trained well to do that.
The appliance must be installed onto a vertical wall
in a correct vertical way, and flames observation
hole should be in human eyes level (about 140 to
The space of exhaust pipes from ceiling should be
not less than 60cm and from side walls not less than
Caution! The appliance should be equipped with
an exhaust pipe or a chimney. Please pay attention to
the specific regulations for installation required by the
Caution! make sure not to mount the appliance
on a wall contains inflammable materials, if mounted
on an inflammable material's wall like wood put heat
insulation material between the wall and the appliance
It is prohibited to put any inflammable , exploding
or corrosive materials close to the appliance ,never
block the exhaust pipe with anything.
No cables ,electric appliances or gas pipes can be
placed above the appliance, Keep the heater away
from heat sources such as gas cockers.
The appliance must vertical on mounting.