Installation Manual of Room Air Conditioner
Necessary Tools for Installation
Hole core drill
Spanner(17,19 and 26mm)
Gas leakage detector or
Before inserting power plug into receptacle, check the voltage without fail.
The power source is the same as the corresponding name plate.
Install an exclusive branch circuit of the power.
A receptacle shall be set up in a distance where the power cable can be
reached.Do not extend the cable by cutting it.
Drawing for the installation of indoor and outdoor units
The models adopt HFC free refrigerant R410A
more than 5cm
Arrangement of piping
The marks from
in the ﬁgure are the
The distance between
the indoor unit and the
ﬂoor should be more
Please be subject to the actual product purchased , the above picture is just for your reference.
Read this manual before installation
Explain sufﬁciently the operating means to the user according to this manual.
more than 10cm
more than 10cm
Selection of Installation Place
Place, robust not causing vibration, where the body can be supported sufﬁciently.
Place, not affected by heat or steam generated in the vicinity, where inlet and outlet of the
unit are not disturbed.
Place, possible to drain easily, where piping can be connected with the outdoor unit.
Place, where cold air can be spread in a room entirely.
Place, nearby a power receptacle, with enough space around. (Refer to drawings).
Place where the distance of more than lm from televisions, radios, wireless apparatuses
and ﬂuorescent lamps can be left.
In the case of ﬁxing the remote controller on a wall, place where the indoor unit can
receive signals when the ﬂuorescent lamps in the room are lightened.
Place, which is less affected by rain or direct sunlight and is sufﬁciently ventilated.
Place, possible to bear the unit, where vibration and noise are not increased.
Place, where discharged wind and noise do not cause a nuisance to the neighbors.
Place, where a distance marked
Attention must be paid to
the rising up of drain hose
is available as illustrated in the above ﬁgure.
Optional parts for piping
Saddle (L.S) with screws
Connecting electric cable
for indoor and outdoor
Heating insulating material
Piping hole cover
Floor ﬁxing dimensions of the
outdoor unit (Unit:mm)
Fixing of outdoor unit
Fix the unit to concrete or block
with bolts (10mm) and nuts ﬁrmly
When ﬁtting the unit to wall
surface, roof or rooftop, ﬁx
a supporter surely with nails
or wires in consideration of
earthquake and strong wind.
If vibration may affect the
house, ﬁx the unit by attaching a