INDOOR KIT INSTALLATION & ACTIVATION GUIDE
The Sensi™ Predict kit is designed for conventional, residential HVAC equipment (furnace, AC, & heat
pumps) in homes that have Internet access. The Sensi Predict system acts as a monitor only and does not
provide any HVAC control.
As the installing technician, it is your responsibility to know what requirements, hazards and precautions
exist, and to install the monitoring system in a safe manner.
Do not alter the mounting of parts within the HVAC equipment.
• Installer must be a qualified technician, familiar
with installation and service of HVAC equipment,
associated wiring, and electrical codes.
• Follow all local and national
codes and ordinances.
• The Sensi Predict power transformers are
designed for connection to 120VAC or 240VAC volt
electric powers within existing HVAC chassis only.
• After installation or replacement, follow the HVAC
manufacturer's recommended instructions to
ensure proper operation of the HVAC equipment.
• Labeling any HVAC wires that need
to be disconnected during the
installation is recommended.
Operating Temp -40°F to 158°F
Storage Temp -40°F to 176°F
Line Voltage Inputs 90-132VAC / 180-
Control Line Voltage 24VAC at 60Hz
The Sensi Predict Contractor PRO Portal can be accessed at sensipredictpro.com
For login support, contact your office administrator. For support within the PRO Portal, call 1-877-424-1715.
FAILURE TO COMPLY WITH THE
FOLLOWING WARNINGS COULD RESULT
IN PERSONAL INJURY OR PROPERTY
• Disconnect electrical power supplies before
installation or servicing.
• Do not exceed specified voltages. Only
power transformers should be connected
to line voltage. All other wires shall only
connect to low voltage (24 VAC). Safely
route and secure all wiring after installation.
• Protect powered devices from direct
contact with water. Replace any device
exposed to water. (Does not apply to
Supply Air Sensors, Return Air Sensors,
Suction Line Sensors, Liquid Line Sensors.)