Cleaning and maintenance must be carried out when À lter lamp lights. Before cleaning, stop
operation and switch off the power supply.
Clean the pre-À lter, as it removes dust inside the room. In case the pre-À lter is full of dust, the air
Á ow will decrease and the cooling capacity will be reduced. Further, noise may occur. Be sure to
clean the À lter following the procedure below.
Open the front panel and remove the À lter
Gently lift and remove the air purifying À lter
from the À lter frame.
Vacuum dust from the pre-À lter and air purifying
À lter using vacuum cleaner. If there is too much
dust, rinse under running tap water and gently
brush it with soft bristle brush. Allow À lters to
dry in shade.
Re-insert the air purifying À lter to the À lter
frame. Set the pre-À lter with "FRONT" mark
facing front, and slot them into the original
After attaching the pre-À lters, push the front
panel at three arrow portions as shown in
À gure and close it.
Air purifying À lter should be cleaned every month or sooner if noticeable loading occurs. When
used overtime, it may loose its deodorizing function. For maximum performance, it is recommended
to replace it every 1 year depending on application requirements.
Do not wash with hot water at more than 40°C. The À lter may shrink.
When washing it, shake off moisture completely and dry it in the shade; do not expose it directly
to the sun. The À lter may shrink.
Do not use detergent on the air purifying À lter as some detergent may deteriorate the air purifying
À lter electrostatic performance.
– 17 –