V4055F,G FLUID POWER ACTUATOR WITH MANUAL CONTROL
Table 1. Auxiliary Switch And Valve-closed Indication
Switch Ratings: 112 hp (0.37 kW)
Maximum total connected power to both switches (if used) is
Nominal Opening Time: 13 seconds:
Closing Time: 1 sec maximum when de-energized.
Ambient Operating Temperature Rating:
-40°F to +150°F (-40°C to +66°C) for 60 Hz models; -10°F to
+158°F (-23°C to +70°C) for 50 Hz and 50/60 Hz models.
1. The red READY TO OPEN light will be on if there is
power to the actuator and the rocker switch is in the
2. To open the valve depress the rocker switch to the
VALVE OPEN position and hold until the valve is open
(Red READY TO OPEN light turns off). The valve will
close if the rocker switch is released from the VALVE
OPEN position with the red READY TO OPEN light on.
When purchasing replacement and modernization products from your TRADELINE® wholesaler or distributor, refer to the
TRADELINE® Catalog or price sheets for complete ordering number.
If you have additional questions, need further information, or would like to comment on our products or services, please write or
1. Your local Honeywell Automation and Control Products Sales Office (check white pages of your phone directory).
2. Honeywell Customer Care
1885 Douglas Drive North
Minneapolis, Minnesota 55422-4386
In Canada—Honeywell Limited/Honeywell Limitée, 35 Dynamic Drive, Toronto, Ontario M1V 4Z9.
International Sales and Service Offices in all principal cities of the world. Manufacturing in Australia, Canada, Finland, France,
Germany, Japan, Mexico, Netherlands, Spain, Taiwan, United Kingdom, U.S.A.
Table 2. Electrical Ratings.
Actuator mounts directly to valve bonnet with 2 setscrews,
positioned 90 angular degrees apart. Valve and actuator
can be mounted in any position.
Mounting Dimensions: See Fig. 1.
130928 Red Indicator Lamp.
133568 Auxiliary Switch Bag Assembly.
133569 Valve-Closed Indication Switch Bag Assembly.
Approvals: UL and FM. IRI Approvable.
Electrical Ratings: See Table 2.
3. To close the valve depress rocker switch to VALVE
CLOSED position. The rocker switch stays in the valve
closed position when released.
4. The valve automatically closes on power loss. It must
be manually reopened using the rocker switch.