5 x 16A relay & Open Protocol Controller
Single Phase Supply - 1 phase at 0.15A
5 x Feed thru Outputs Rated at 16A
Power outputs are Latching Relays
Manual Overrides for each channel
Powerful Internal PLC - Custom scripts can be written to
provide process control based on conditional logic
Dry Contact Interface - An Auxiliary dry contact interface is
provided. The factory settings will cause this input to transmit
network identification information
Many Control Options - Control of this device can be via a
combination of methods, eg. serial control port, relay
contacts, push button wall stations, infrared receivers and
Simple Installation - DIN Rail mount facilitates installation.
All connection terminals are accessible without disassembly
Warning – This device is a class A product. In a domestic environment this
product may cause radio interference, in which case the user may be required to
take adequate measures.
Read Instructions – We recommend that you read this Instruction Manual prior
to commencement of installation.
Manual Override Switches - These switches do not provide permanent
isolation. Isolate at the supply before performing work on load circuits.
Special Programming – This device will only operate in basic modes unless
programmed via a computer.
If programming is required, contact your local
agent for details. Once the data cable is connected to the devices, the factory
default settings will allow any control panel to operate all channels in all
Power Sources – This device should only be operated from the type of supply
specified on the front cover. This device must be earthed.
Feed Thru Output Circuits – The load on a circuit should not exceed the
specified capacity of 16A. Loads should be calculated to ensure that the overall
maximum capacity of 80A is not exceeded. This device should be fed via a HRC
fuse or MCB. Output circuits are suitable for Single Phase or Three Phase Star
(with Neutral) only, Delta wiring is not supported.
Mounting Location – Install in a dry, well-ventilated location. Controllers may
emit some mechanical noise. Take this into account when deciding the mounting
Data Cable – Use screened, stranded RS485 data cable with three twisted pairs.
Segregate from mains cables by 300mm minimum. Connect devices in a 'daisy
chain'. A data cable that is connected to an energised device is live. Do not cut
or terminate live data cables.
To reduce the risk of fire or electric shock, do not expose
this device to rain or moisture. Do not energise unless the
front cover is in place.
This device must be earthed.
Installation, programming and maintenance must be
carried out by qualified personnel.