Signal Dimmer Controller
Single-phase supply – 100 - 240 VAC at 0.5A
12 individually controlled lighting driver channels – each
High output capacity – each of the 12 channels is capable of
driving the following:
DALI: max 80 drivers per channel or 300 total
DSI: max 100 drivers per channel or 375 total
0-10V: 50mA sink or source per channel
LED status indicators and override switches – for each of the
Powerful internal PLC – allows custom scripts to enable process
control based on conditional logic
Dry contact interface – factory settings enable this interface to
Many control options – device is controllable via a combination of
methods, including a serial control port, relay contacts, push-button
wall stations, infrared receivers and timeclocks
100 – 240 VAC
Read Instructions – We recommend that you read this guide prior
to commencement of installation.
Special Programming – Once powered and terminated correctly
this device will only operate in basic mode. If network terminations
are correct, a new Dynalite user interface turns all lighting channels
on from button 1 and off from button 4. Commissioning can only
begin once the full network has been tested. Advanced functions
are commissioned via Envision software. If commissioning services
are required, contact your local distributor.
Check Connections – Tighten all load-bearing screw connections,
as vibrations from transport can cause the terminal block screws to
Power Sources – This device must only be powered by the supply
Output Circuits – The load on each circuit must not exceed the
or 50mA sink or source for 1-10V.
Mounting Location – Install in a dry, well-ventilated location.
Controllers may emit some mechanical noise. Take this into
account when deciding the mounting location.
Data Cable – Use screened, stranded RS485 data cable with three
twisted pairs. Segregate from mains cables by at least 300mm.
is connected to an energized device is live. Do not cut or terminate
live data cables.
2 x RJ12