RP-2002 & RP-2002E Agent Release Control System
NORMAL - Only AC POWER is illuminated green.
All other indicators are off. LCD display will read SYSTEM
WHEN AUDIBLE DEVICES ARE SOUNDING -
Discharge has occurred if DISCHARGE Indicator is on.
Discharge timer has timed out if DISCHARGE Indicator is flashing.
FOR AN ALARM
1. Evacuate the protected area
2. Notify the monitoring service and/or the Fire Department immediately. Tell them briefly what happened and what
your current status is.
Phones: ____________________________ _________________________________
3. If the Fire Department is responding, be prepared to provide directions to arriving firefighters.
FOR TROUBLE ONLY
1. Notify the monitoring service and/or Fire department if this panel is connected to either one, and tell them
what is happening.
2. Silence audible devices by unlocking and opening the panel and pressing the ACKNOWLEDGE/STEP button. The
TROUBLE indicator will remain illuminated yellow. Contact authorized service personnel immediately! (See Below).
DO NOT ALLOW TROUBLE CONDITIONS TO REMAIN LOGGED IN THE SYSTEM. THE PROTECTION THE
SYSTEM OFFERS HAS BEEN COMPROMISED, OR ELIMINATED WHEN A TROUBLE CONDITION EXISTS.
To return to normal after an alarm
1. Do not enter the protected area until safe to do so.
2. Clear all initiating devices. Smoke detectors will not reset
if there is still smoke in the area.
3. Reset the control panel (PRESS the RESET button)
Power failure or brownout
If AC power drops too low or fails, AC POWER indicator will
extinguish, the system TROUBLE indicator will turn on yellow, and
the panel buzzer and any other audible trouble devices will sound.
Contact authorized service personnel immediately. See below.
Activation of Manual Release Switch will override Predischarge
Delay and override an active Abort Release Switch, resulting in an
immediate agent release.
In the event of trouble, contact the
local Notifier Service Representative
Telephone Number: ________________________
PANEL KEY - The key to open the panel can be found at the
Manual activation (Fire Drill or otherwise)
Notification Appliance Circuits (NACs) can be activated by
pressing and holding the DRILL button for at least two
NOTE: You may want to disconnect municipal box by sliding
Notification Appliance Circuits may be silenced by pressing the
ALARM SILENCE button. ALARM SILENCED will turn on yellow.
Subsequent alarms will reactivate circuits. Press the RESET
button to clear the "silenced" condition.
NOTE: Notification Appliance Circuits may be programmed as
nonsilenceable. Also, Signal Silence Inhibit, if enabled, will
prevent silencing of NACs for one minute after an alarm (see
To test the indicators, LCD display and piezo
Press and release the RESET button and check all indicators/
LEDs. Every indicator/LED should be on, LCD shows all pixels
on, piezo sounder beeps.
For more information, refer to the RP-2002 & RP-2002E Manual,
Document #53039. It is kept in the following location:
THIS SHEET SHALL BE FRAMED ADJACENT TO
DISCONNECT switch, located on 4XTM module, to its
disconnect position (to the right). If a DACT is con-
nected, notify the monitoring service before conducting
any fire drills or tests.
THE CONTROL PANEL
Rev. A 3/05/07 ECN 07-132