Setting the Auxiliary Output
Switch 4 on the DIP switch determines how the auxiliary power operates.
The PAD-3 checks switch 4 only when powering up. If you change this switch, you must push switch SW2
momentarily to reset the unit to recognize the new switch setting.
Figure 5-2. Setting DIP Switch 4
Switch 4 OFF:
Auxiliary Power Output always on.
Switch 4 ON:
Auxiliary Power Output will shutdown 30 seconds after an AC Power fault
and the unit is running on battery.