E6581279 TOSVERT VF-AS1 PROFIBUS-DP Option Instruction Manual PDP002Z Notice Make sure that this instruction manual is delivered to the end user of the PROFIBUS option for the VF-AS1. Read this manual before installing or operating the PROFIBUS option And keep it in a safe place for reference.
E6581279 Safety precautions On the inverter and in its instruction manual, important information is contained for preventing injuries to users and damages to assets and for proper use of the device. Read the instruction manual attached to VF-AS1 along with this instruction manual for completely understanding the safety precautions and adhere to the contents of these manuals.
E6581279 ■ General Operation Danger ▼ Never disassemble, modify or repair. Doing so could result in electric shock, fire and injury. For repairs, call your sales agency. Disassembly prohibited ▼Do not attach this option to any inverter other than the VF-AS1. Doing so could result in electric shock or fire.
E6581279 ■ Wiring Danger ▼ Shut off power when installing and wiring this option. Wait at least 15 minutes and check to make sure that the charge lamp (VF-AS1) is no Mandatory longer lit. ▼ Electrical construction work must be done by a qualified expert. Installation or connection of input power by someone who does not have that expert knowledge may result in fire or electric shock.
E6581279 Introduction Thank you for purchasing a “VF-AS1 PROFIBUS Option (PDP002Z),” for TOSVERT VF-AS1 inverter. Installing this option in the VF-AS1 and using it together, data communication can be made with a host computer or other device via PROFIBUS DP (DP-V0). Please read the entire manual carefully before attempting to control your inverter via PROFIBUS connection.
E6581279 Contents 1. OVERVIEW ..........................6 2. EXTERIOR FEATURES ......................... 7 2.1. PROFIBUS connector......................8 2.2. Status indicator ........................8 3. INSTALLING THE PDP002Z......................9 4. CONNECTING TO THE NETWORK....................10 4.1. Installation method ......................10 4.2. Setting a station address ..................... 11 5.
E6581279 1. Overview The PDP002Z option allows the VF-AS1 inverter to be connected as a slave (DP-V0) into a PROFIBUS network. Up to 126 stations* can be connected to the network (* including a master. If no repeater is provided, up to 32 stations can be connected to each segment). VF-AS1 VF-AS1 Master...
E6581279 2. Exterior features The external view of this option and the name of each part are shown below. Status indicator (Refer to Section 2.2) Panel mounting tabs (Refer to Section 3) Address switch （Refer to Section 4.2） PROFIBUS connector (Refer to Section 2.1) Danger ▼...
E6581279 2.1. PROFIBUS connector Used to connect PROFIBUS network cables. The connector is a D-Sub connector with 9 pin female and the connector pin allocation described below follows the PROFIBUS standard. Pin number Symbol Signal type Reserved Reserved RxD/TxD-P Send/receive data (+) CNTR-P Control signal DGND...
E6581279 3. Installing the PDP002Z Install the PROFIBUS option to VF-AS1 as follows: * When this option is used together with the IO card option, attach this option to the front panel side. (1) Turn off input power of VF-AS1 and wait for at least 15 minutes and then check that the CHARGE lamp on VF-AS1 is no longer lit.
E6581279 4. Connecting to the network 4.1. Installation method (1) Using the DIP switch on the PROFIBUS option, set a station address (Refer to Section 4.2). (2) Connect a PROFIBUS connector to the PDP002Z. (Refer to Section 2.1.) * If the PDP002Z is located at an end of the bus, connect a terminal resistor to it. (When using a connector with termination resistor , set it ON.) (3) Once all the parameters are set, the power must be cycled to the VF-AS1 for these changes to take effect.
E6581279 4.2. Setting a station address The DIP switch on the circuit board of the option is used to set a station address. Each DIP switch is ON when it is flipped to the lower position. By default, it is factory-configured to 2. The station address must be unique and not match any other device on the network.
E6581279 ON OFF OFF OFF OFF OFF OFF ON OFF OFF OFF OFF OFF ON OFF OFF OFF OFF OFF ON OFF OFF OFF OFF ON OFF OFF OFF OFF ON OFF ON OFF OFF OFF ON OFF ON OFF OFF OFF OFF ON OFF OFF OFF ON OFF OFF OFF OFF OFF...
On the network, the VF-AS1 (including the PDP002Z) serves as a slave device. Using the parameters listed below, set the slave device on the network and its mode of operation. The GSD files used to configure the PDP002Z can be downloaded from the Toshiba Schneider Inverter web site.
E6581279 5.1. f851: Communication Loss Action Setting (Network breaks) This parameter sets up the VF-AS1 response to a loss of communications with the PROFIBUS network. 0: Stop and break of connection The inverter decelerates the motor to a stop and gives the alarm. Commands entered through the network are canceled, and the commands set with parameters cmod and fmod become effective.
E6581279 5.3. f830: PPO TYPE Setting The PPO type of PDP002Z is set up by this parameter. The PROFIBUS-DP protocol uses so-called PPOs (Parameter/Process Data Objects) in cyclic communication. The figures below show the PPO types and configurations that the PDP002Z supports PZD1 PZD2...
E6581279 6. PROFIBUS Local/Remote Operation The example below shows how to configure the VF-AS1 for local / remote operation. <Terminal function> F terminal ... RUN command R terminal... PROFIBUS/Local (Terminal in this example) switching RR/S4 terminal..Operation frequency command <Wiring> VF-AS1 Variable resistor for adjustment 10k ohm...
1. If the product breaks down within one year after delivery, although it is installed and handled properly, and if the breakdown is undoubtedly attributable to a defect in designing or manufacturing by Toshiba Schneider Inverter Corporation, the product shall be repaired free of charge.