READ THOROUGHLY BEFORE INSTALLING
Risk of electric shock
• Turn power off before servicing
– see instructions
G E N E R A L
This luminaire is designed for outdoor lighting
applications, and should not be used in areas of limited
ventilation, or in high ambient temperature enclosures.
Best results will be obtained if installed and maintained
according to the following recommendations.
U N P A C K I N G
This luminaire has been properly packed so that no parts
should have been damaged during transit. Inspect to
These instructions do not purport to cover all details or variations in equipment nor to provide for every possible contingency to be met in connection with installation, operation or
maintenance. Should further information be desired or should particular problems arise which are not covered sufficiently for the purchaser's purposes, the matter should be referred
to GE Lighting Solutions.
M O U N T I N G
mounting, pipe mounting, or wall mounting.
a flat surface. Mounting adapters are available for
installation on poles, crossarms, pipes, etc.
bolt used for attachment to such mountings. The 7/16-inch
holes on either side permit additional anchoring, where
required. Tighten side trunnion bolts to 18 -22 foot pounds.
mounted on 1-7/8-inch O.D. through 2-3/8-inch O.D. or
2-7/8-inch O.D. through 3-inch O.D. pipes. Three set screws
are used to clamp the floodlight securely to the pipe.
Tighten side trunnion bolts to 18 -22 foot pounds.
is provided with four (4) 0.438-inch clearance holes spaced
4.375(H)x2.875(V) inches for mounting.
Unit will fall if not installed properly
• Follow installation instructions
This floodlight is provided with either trunnion
NOTE: The unit may be mounted to point from
straight up to straight down but in no case may the
ballast be located above the optical.
NOTE: For aimed-up application, remove two
screws from rear bottom corners of back housing
and fill two holes on bottom front door with RTV.
TRUNNION MOUNTED UNITS — Mounted directly on
The trunnion bracket has a clearance hole for a 5/8-inch
PIPE MOUNTED UNITS — The slipfitter can be
WALL MOUNTED UNITS — The wall mounting plate