READ THOROUGHLY BEFORE INSTALLING
Risk of electric shock
• Turn power off before servicing
– see instructions
NOTE: Make all electrical connections in accor-
dance with the National Electrical Code and any
applicable local code requirements.
NOTE: This luminaire is equipped with a safety
circuit to prevent lamp operation if the reflector
lens is broken. Complete optical assembly must
be replaced if the reflector lens is broken.
This luminaire is shipped with the lamp installed.
This luminaire is designed for use in outdoor applica-
tions and should not be used in areas of limited ventila-
tion or high ambient temperature enclosures unless
otherwise stated on nameplate. Install and maintain it
according to the following recommendations.
NOTE: Connect ground lead to the green lead,
green ground screw on housing or terminal block
Replace power fuses only with fuses of the same
type and ratings.
Risk of fire
• Keep combustible materials away
from lens – see instructions
• Use lamps specified on nameplate
Step 1 — POWER CABLE INSTALLATION
A . Disconnect Power
B . Remove Cover (a)
C . Loosen clamp (b)
Insert cable thru
clamp and grommet
D . Splice leads (c)
to power cable
E . Tighten clamp (b)
F . Replace cover (a)
NOTE: Use 9/16 OD-
3 conductor AWG #14
SEO 105C cable
These instructions do not purport to cover all details or variations in equipment nor to provide for every possible contingency to be met in connection with installation, operation
or maintenance. Should further information be desired or should particular problems arise which are not covered sufficiently for the purchaser's purposes, the matter should be
referred to GE Lighting Solutions.
Unit will fall if not installed properly
• Follow installation instructions
NOTE: Verify that supply voltage is correct by
comparing it to nameplate.
Do not place combustible materials within 7 feet
(2 meters) of the front of the reflector lens.
Step 2 — LUMINAIRE MOUNTING