On an annual basis, maintenance is required to ensure TrueDRY runs at peak efficiency.
Unplug TrueDRY DR65 before beginning
service. Press down on the quick-
release button and remove the duct
Using a 1/2-in. hex drive or standard
screwdriver, remove the three screws
on each side of the TrueDRY DR65. The
cabinet can then be removed. Using
a damp cloth, wipe excess dust and
debris from blower, refrigerant coils, and
compressor coils. Reattach cabinet and
collars when finished.
TrueDry DR65 Dehumidification System
Remove filter (50049537-005) and
replace with new filter.
Check the drain connection and drain
line to ensure it is clear of debris and
sludge. Ensure all hose connections
are secure once maintenance of the
drain lines is complete.
When service is complete, initiate a
call for dehumidification and check
that the compressor and fan activate.
If using the VisionPRO IAQ or TrueIAQ
controls, reset maintenance remind-