INSTALLATION MANUAL ROOM AIR CONDITIONER WALL MOUNTED TYPE HSU-24HEA03/R2-I Read this manual before installation Explain sufficiently the operating means to the user according to this manual. NO.0010523237...
Saddle(L.S) with screws Connecting electric cable for indoor and outdoor Drain hose Heating insulating material Piping hole cover The marks from in the figure are the parts numbers. The distance between the indoor unit and the floor should be more than 2m.
Before inserting power plug into receptacle, check the voltage without fail. The power source is the same as the corresponding name plate. Install an exclusive branch circuit of the power. A receptacle shall be set up in a distance where the power cable can be reached. Do not extend the cable by cutting it. Selection of pipe...
In case of left side piping, cut away, with a nipper, the lid for left piping. In case of left-rear piping, bend the pipes according to the piping direction to the mark of hole for left-rear piping which is marked on heat insulation materials.
Indoor unit 1. Insert the drain hose into the dent of heat insulation materials of indoor unit. 2. Insert the indoor/outdoor electric cable from backside of indoor unit, and pull it out on the front side, then connect them. 3. Coat the flaring seal face with refrigerant oil and connect pipes.
Be careful that matters, such as wastes of sands, etc. shall not enter the pipe. The standard pipe length is 7.5m. If it is over 10m, the function of the unit will be affected. If the pipe has to be lengthened, the refrigerant should be charged, according to 50 g/m. But the charge of refrigerant must be conducted by professional air conditioner engineer.
Otherwise, there will be refrigerant into air conditioner according to the amount marked on abnormal high pressure in the system to make it crack and lead to the name plate. personal injuries.
Please pour water in the drain pan of the indoor unit, and confirm that drainage is carried out surely to outdoor. In case that the attached drain hose is in a room, please apply heat insulation to it without fail.
The products are fulfilled with the requirements in the directive 2002/95/EEC of the local and national legislation. Air conditioners must be European parliament and of the council on the Restriction of the use of Certain Haz- treated at a specialized treatment facility for re-use, recycling and recovery.
WEEE cias negativas para el entorno y para la salud de las personas. Contacte, por De acuerdo con la directiva 2002/96/CE del parlamento Europeo, Informa- favor, con el instalador o con las autoridades locales para obtener más infor- mos al consumidor acerca del reciclage de los productos Electrónicos y...
IMPORTANT INFORMATION REGARDING THE REFRIGERANT USED This product contains fluorinated greenhouse gases covered by the Kyoto The filled out label must be adhered in the proximity of the product charging Protocol. Do not vent into the atmosphere. port (e.g. onto the inside of the stop valve cover).
INFORMACIÓN IMPORTANTE EN RELACIÓN AL REFRIGERANTE UTILIZADO Este producto contiene los gases fluorados de efecto invernadora regulados La etiqueta rellenada debe pegarse cerca de la conexión de carga del pro- por el Protocolo de Kioto. No vierta gases a la atmósfera.