SOL MODULE CONTROLLER_IM_05747A-00_EN.indd 2 2016-01-20 오후 12:00:16...
DVM CHILLER Installation manual Module control MCM-A00N • Thank you for purchasing this Samsung air conditioner. • Before operating this unit, please read this installation manual carefully and retain it for future reference. SOL MODULE CONTROLLER_IM_05747A-00_EN.indd 3 2016-01-20 오후 12:00:16...
Contents PREPARATION Safety information INSTALLATION Checking before the installation Accessories External dimension Installing the module control Installing the module control DVM CHILLER Tracking Connecting the module control Restarting the module control communication Module control error display SETTING Setting the service mode Service mode setting Service setting mode Setting the option (Example)
PREPARATION Safety information This installation manual explains how to install a Module control. Please read this manual thoroughly before installing the product. (Please refer to an appropriate installation manual for any optional product installation.) WARNING Hazards or unsafe practices that may result in severe personal injury or death. CAUTION Hazards or unsafe practices that may result in minor personal injury or property damage.
Safety information CAUTION Do not install the product in a place where it is or might be exposed to inflammable gas leakage. y There is risk of fire or explosion. Do not install the product in a place where it will be exposed to oil or vapor etc. y If the product is installed in a place where it is exposed to oil, vapor or sulphur dioxide, parts of the product may get damaged or product may function abnormally.
INSTALLATION Checking before the installation Accessories Item Module control M4xL16 screws User manual Installation manual Quantity Shape CAUTION • The installation must be performed by a qualified expert. • Before installing the module control, make sure to check if it is turned off. •...
Installing the module control Installing the module control 2 Arrange the power and communication cable. y Place the cable through openings in the 1 Disassemble the module control. rear cover. y Push a hook with one hand and push up another hook with another hand to disassemble the rear cover.
3 Fix the rear cover. 4 Connect the power and communication cable. y Before fixing the rear cover, allow 10 mm(0.4 inch) or more space for upper, y Connect the communication cable (F3, F4) left, and right sides and 50 mm(2 inch) to the PBA terminal on the back of the space for bottom side.
Installing the module control • Specification of compressed U-terminal CAUTION for connecting module control PBA • The power and communication wire of the module control and the power wire of DVM CHILLER should be installed separately. Stud Ø – Electrical interference may cause the module control to malfunction.
DVM CHILLER Tracking When installing the module control and then turning it on, the tracking will be performed automatically. y To perform the tracking again, press the button at the same time for more than 5 seconds. y During the tracking, the total number of currently searched DVM CHILLERs will be displayed on the display.
Installing the module control Connecting the module control Module control 1:1 Install one DVM CHILLER to a single module control. CHILLER F3, F4 Module control 10 English SOL MODULE CONTROLLER_IM_05747A-00_EN.indd 10 2016-01-20 오후 12:00:19...
Module control 1:N Install N (maximum 16) DVM CHILLERs to a single module control. CHILLER 1 CHILLER 2 CHILLER 16 F3, F4 F3, F4 F3, F4 Module control CAUTION • Only a single module control can be connected to DVM CHILLERs. •...
Installing the module control Restarting the module control communication After changing the installation status (changing the number of the installed DVM CHILLERs or their numbers or resetting the group/module) of DVM CHILLERs, the module control communication must be restarted. Press for over 5 seconds.
When an error occurs in the module control Only the error code will be displayed. y Example) When error 601 occurs from the Module control Module control error codes Error Description codes Communication tracking error between a module control and DVM CHILLERs The maximum number of DVM CHILLER installation is exceeded.
SETTING Setting the service mode Service mode setting Item Description Main menu Displays a main menu value of the service mode table. Sub menu Displays a sub menu value of the service mode table. Page Displays a Page value of the service mode table. Data Segment Displays a Data value of the service mode table.
1 Start the service mode. 6 Save the data setting value. Press for over 3 seconds 7 Complete the service mode. CAUTION • To make it work correctly, you have to press the center of the buttons at the same time. NOTE 2 Select a main menu number.
Setting the service mode Service setting mode y After saving the setting, the DVM CHILLERs and the module control may be initialized if it is necessary. y When entering the service mode during the tracking, you can enter the Data stage on the Main menu 4,5,6,9 (Save at DVM CHILLER) but you cannot change the setting.
Main Default Function Page Data Segment Save menu menu value Save at 0 - 12-hours, Setting type of time Module 1 - 24-hours control 0 - Normal, Check for timer IC error 1 - Error Initializing service mode 0 - Disuse, setting value 1 - Reset Checking micom codes of the...
Setting the service mode Main Default Function Page Data Segment Save menu menu value 0 - Default value (100 %) 1 - 95 % 2 - 90 % 3 - 85 % 4 - 80 % Save at Module 5 - 75 % Demand level number 6 - 70 %...
Main Default Function Page Data Segment Save menu menu value Outdoor Main temperature Save at AirCool1 unit standard 1 (for Water law) number (0 ~ 20 °C) in CHILLER cooling mode Outdoor Main temperature Save at AirCool2 unit standard 2 (for Water law) number (30 ~ 40 °C) in CHILLER...
Setting the service mode Main Default Function Page Data Segment Save menu menu value Outdoor Main temperature Save at AirHeat1 unit standard 1 (for Water law) number (-20 ~ 5 °C) in CHILLER heating mode Outdoor Main temperature Save at AirHeat2 unit standard 2 (for Water law)
Main Default Function Page Data Segment Save menu menu value Heating set Main temperature Save at Theat2 unit standard 2 (for Water law) number (35 ~ 55 °C) in CHILLER CHILLER heating mode detailed Operation pattern setting 2 for modules 0 - Standard Save at Module (When operating...
Setting the service mode Main Default Function Page Data Segment Save menu menu value Initialize factory setting of the module control 0 - No use, 1 - Reset (Initialize user/ service mode setting value) Reset Initialize power 0 - No use, master 1 - Reset Initialize DVM...
y Select a standard for Water law when operating cooling or heating. Water law is to change the water outlet temperature, considering demand load changes according to outdoor or indoor temperature. – According to outdoor temperature Theat1 Tcool1 Tcool2 Theat2 AirCool1 AirCool2 AirHeat1...
Setting the service mode y A main unit of a gourp or a module will be displayed. y When setting a group, the value for a main unit of the group must be set. y When setting "Standard pattern" for a group, you must set an operation pattern for each module in the group.
Setting the option (Example) It is an example to change the temperature display unit from Fahrenheit (°F) to Celsius (° C). 1 Start the service mode. Press for over 3 seconds 2 Select a desired number in the main menu. ...
Setting the service mode 4 Select a desired number in Page y The data value of the Page will be set at the same time. Select 2 5 Set Data value. y Setting value 0 - Celsius (° C), setting value 1 - Fahrenheit (°F) ...
Setting the service mode Module or group operation Module/group operation is to combine multiple units according to modules or groups of a single water pipe system and to operate them depending on working condition. Installation example) Module control F3, F4 Main Main Main...
Setting module and group (Example) It is an example to set 6 units to modules and groups. y The example explains how to set the units to 1 group and 1 module (No.3). y Recommended deciding and entering numbers for modules and groups of units and a main unit in advance, since you have to set numbers for modules and groups by each unit.
Setting the service mode 1 Start the service mode. Press for over 3 seconds 2 Select a desired number in the main menu. Select 9 3 Select a desired number in the sub menu. Select 1 4 Select a desired number in Page y The smallest number will be displayed among the numbers of currently connected DVM CHILLERs.
6 Set a group number (Data2). y '-' will be displayed if the group number is not set. Select 2 7 Complete the option setting. NOTE • 2 or more modules must be selected for one group. –...