SAFETY PRECAUTIONS SAFETY PRECAUTIONS • This product must be installed by an installation professional from an LG authorised service center. • Any issues stemming from an installation by an unauthorised person is the responsibility of the user and will not be covered by warranty.
SAFETY PRECAUTIONS - If the product is not secured during installation, it may fall or malfunction. • Read the manual thoroughly to correctly install the product. - Follow the below precautions properly; else it might result in a fire disaster, risk of incurring electric shock injuries or product malfunctioning.
SAFETY PRECAUTIONS • Do NOT disassemble, repair, or revamp the product arbitrarily. - Follow the below precautions properly; else it might result in a fire disaster, risk of incurring electric shock injuries, product malfunctioning or damage to property. • Children and the elderly should use the product under the supervision of a guardian. - Follow the below precautions properly;...
SAFETY PRECAUTIONS • Installation work must be performed in accordance with the national wiring standards by authorized personnel only. This equipment shall be provided with a supply conductor complying with the national regulation. • The appliance is only to be used with the power supply unit provided with the appliance. •...
WEEE collection point. For the most up to date information for your country please see www.lg.com/global/recycling Disposal of waste batteries/accumulators 1. This symbol may be combined with chemical symbols for mercury (Hg), cadmium (Cd) or lead (Pb) if the battery contains more than 0.0005% of mercury, 0.002% of cadmium or 0.004% of lead.
ACP 5 FUNCTIONS AND SPECIFICATION ACP 5 is the central controller that can manage up to 256 equipments in one space individually or as combined. ACP 5 can monitor or control the equipments installed in each room of the building from the places such as the management office of a building or the administration office of a school.
⑧ USB port For software update and data backup ⑨ Power switch Switch to turn on or off the power of the ACP 5 ⑩ Ethernet port Ethernet port to connect to internet and AC Manager 5 ⑪ SD card slot...
ACP 5 FUNCTIONS AND SPECIFICATION ACP 5 Hardware speciﬁcation ACP 5 hardware specification is as follows. Category Description ① Operating temperature 0 °C ~ 40 °C ② Rated voltage 12 V ③ Rated current Max 2.3 A • Ethernet 10 / 100 BASE-T •...
Installing ACP 5 This chapter describes how to install the ACP 5 to use. In order to use the ACP 5, the installation should be performed by the following order. STEP 1. Check the cautions during the ACP 5 installation Before installing the ACP 5, check the cautions.
To one RS-485 port, all of 256 indoor units, which is the maximum number that To connect ERV equipment, it is recom- can be connected to the ACP 5, may be con- mended to use the ports other than RS- nected. But, to improve the communication 485 communication ports which are con- nected to air conditioners.
When the ACP 5 is interconnected with the AC Manager 5, the ERV can be installed together and controlled. The above figure shows the example that sets the addresses of 30 and 31 to the ERV...
RS-485, and LAN cable. ing the environment of the site. • Install DIN RAIL. • Hook the top part of the ACP 5 on DIN RAIL. • Push the main body of the ACP 5 until you hear the sound of installation.
INSTALLING ACP 5 Fixing the ACP 5 to the wall ACP 5 can be installed by fixing to the wall. To install the ACP 5 in an adequate place, pro- ceed according to the following explanation. It explains here on how to install the ACP 5 with...
After connecting the ACP 5 to various devices via the cable, the network environment of the In such case, Ethernet cable shall be connect- ACP 5 should be set by driving the ACP 5. The ed as a cross cable. following information should be set for using Use Ethernet cable to connect to LAN port of the ACP 5.
Turn on the ACP 5 to set the network environment of the ACP 5. When the power switch is turned on, the ACP 5 booting screen is displayed on the LCD as shown at the following figure, and when booting is completed, the initial ACP 5 screen is dis- played.
The following explains how to log in and out of ACP 5. ACP 5, can be controlled either by the equipment or the web. If you enter the IP address of the ACP 5 in the address bar of the command window of web browser (Run>cmd>ipconfig) without the installation of another program, the central control program ACP 5 Web server is executed automatically.
User manual You can view the user manual as follows. In ACP 5 log-in screen, input ID and password and touch [Log in] button. Press 'Help' at the top right side of ACP 5 screen. - The user manual is displayed.
Web GUI does not Please check LAN cable and the power supply of Hub. run. ACP 5 in the lock feature is enabled, the remote control func- Indoor remote control does tion is not set.Peak control state must function setting from not work.
EU Representative : LG Electronics European Shared Service Center B.V. Krijgsman 1, 1186 DM Amstelveen, The Netherlands Manufacturer: LG Electronics Inc. Changwon 2nd factory, 84, Wanam-ro, Seongsan-gu, Changwon-si, Gyeongsangnam-do, KOREA...