Pro th3000 series non-programmable digital thermostat (36 pages)
Summary of Contents for Honeywell e7w
FOR ALL UNITS IN CARTON. DO NOT THROW AWAY! INSTALLATION REQUIREMENTS Required Installation Hardware • Four 6-32 × 1.5” Philips Pan head screws (provided with e7w) if attaching to a 4X4 electrical junction box. • Four AA alkaline batteries; provided with e7w.
Smart Wall Mounting Plate. Location If mounted on a single-gang box, the right side (keypad side) of the e7w overlaps the wall area to Select a location about 1.5m (5ft.) above the floor the right. with good air circulation at average temperature.
Battery Details rect terminal. b. Check the battery voltage. 6. Hook the tabs at the top rear of the e7w housing into the matching depressions at the top of the Smart Mounting Plate and ro- tate the bottom of the housing toward the wall until it snaps into place.
WIRELESS EMS THERMOSTAT - INSTALLATION INSTRUCTIONS Specifications Mounting Standard US Double Gang: w/o Spacer Ring Standard US Single Gang: w/o Spacer Ring Standard UK Single Gang: w/o Spacer Ring Dimension L 120mm x W 120mm x H (23) mm (w/o spacer) Ambient Operating 41 to 149 °F (5 to 40 °C), 0-95% RH non-condensing...
WIRELESS EMS THERMOSTAT - INSTALLATION INSTRUCTIONS INITIAL SETUP Note: Before going through the initial setup se- The five-digit number is comprised of three quences, ensure the thermostat is mounted and fields: highest digit, middle two digits, low- connected to the Smart Wall.
To configure the HVAC controller, wireless mo- tion sensors, doors/windows/balcony switches with e7w, you need to set e7w into Ser- vice Mode. To enter Service, follow the below steps: 1. Press and hold FC key. 2. Press and release MODE.
WIRELESS EMS THERMOSTAT - INSTALLATION INSTRUCTIONS BINDING AUXILIARY DEVICES 3. Use the UP/DOWN arrow buttons to change the displayed value range from 0 to 255. Set the Io value to the desired I/O map number. Note: 4. Press FAN to initiate a reverse bind or press Before binding or verifying auxiliary devices.
WIRELESS EMS THERMOSTAT - INSTALLATION INSTRUCTIONS STANDARDS AND APPROVALS Note 1 We have a choice of the IEC based path or the updated version of Spec. 24. Considera- • Product Standard − EN 60730-1:2011 and tions: EN 60730-2-9:2010 (covers EMC and LVD •...
WIRELESS EMS THERMOSTAT - INSTALLATION INSTRUCTIONS puissent survenir dans une installation par- guarantee that interference will not occur in a ticulier. Si cet équipement cause des interfé- particular installation. If this equipment does rences nuisibles à la réception de signaux de ra- cause harmful interference to radio or television dio ou de télévision, ce qui peut être déterminé...
WIRELESS EMS THERMOSTAT - INSTALLATION INSTRUCTIONS WEEE Directive 2012/19/EC Waste Electrical and Electronic Equip- ment Directive The correct disposal of end-of-life equipment will help prevent potential negative consequences for the environment and human health. Dispose of the packaging and this product in an author- ized collection or recycling center.
The material in this document is for information purposes only. The content and the product described are subject to change without notice. Honeywell makes no representations or warranties with respect to this document. In no event shall Honeywell be liable for technical or editorial omissions or mistakes in this document, nor shall it be liable for any damages, direct or incidental, arising out of or related to the use of this document.