1. Introduction Using UDS-10s or UDS-1100s, a CNC channel to K2100 / K2200 Door Controllers can be set up to communicate over an Ethernet network. Using a method called serial tunneling, two UDS-10s or UDS-1100s encapsulate serial data into packets and transports them over the network.
3. Configuration Each UDS is configured using the DeviceInstaller program supplied by Lantronix. IMPORTANT 1. It is an absolute requirement for the error free operation of the UDS that static IP addresses are used. 2. The DeviceInstaller program must be run on the same subnet as the UDS device. For example, if there is a router between the PC running DeviceInstaller and the UDS then the configuration process will not work.
Select the OK button and the and the DeviceInstaller window is redisplayed: Select (Search the network for devices) and the Search Network window is displayed: Select the PC Network Class Select the Start Search button and any UDS devices on the network will be displayed. Select the Save button and the DeviceInstaller window is redisplayed with a list of all UDS devices detected: 17553v1.0...
10. Select the required device. 11. Select Tools > Device Manager and the Device Management window is displayed: 12. Select (Telnet to Device) and a Telnet session will then start. The DeviceInstaller part of the UDS configuration is complete, the next part is using Telnet. 17553v1.0...
3.2 Telnet Configuration 3.2.1 Connecting to the UDS The UDSs can be connected outside of the DeviceInstaller by using Windows Telnet. To do this, connect using the unit’s assigned IP Address and a port number of 9999. For example: use the command TELNET 192.168.101.52 9999 at the command prompt.
Enter the following information: IP Address The IP Address displayed will be the one that was entered in Section 3.1. Do not change this value; press Enter to move onto the next step. Set Gateway Address Press the Y key, and press Enter. Gateway IP Addr Enter the gateway IP address and press Enter.
3.2.3 PC to Door Controller Configuration After completing Section 3.2.2, the UDS needs to be configured to communicate with the PC. Configuration From the basic parameters menu (see previous section) select 1 and press Enter. Baudrate (9600) 9600 <enter> I/F Mode (4C) ? 4C <enter> Flow (00) ? 00 <enter>...
3.3 Testing Network Connectivity To test if the UDS is accessible over the network: 1. Run the DeviceInstaller program. 2. Select the (Ping Device) and the Ping Device window is displayed: 3. Enter the IP Address of the unit to be pinged, and select the (Ping Device).
4. Configuring the Door Controller The door controller with the UDS attached to it, should have the following options set: 1. System Type 2 2. Baud Rate to 9600 3. Connect Modem set to N. To set these parameters, see the documentation supplied with the door controller. 5.