Intelli-Arc Diagnostic Tool Instruction Sheet Base unit Handheld device...
2. To be installed only on a single phase 120VAC grounded system. 3. The Intelli-Arc Diagnostic Tool is not a protective device. For use only on the load side of a listed branch circuit protection device rated at 20 Amperes or less.
2 AA alkaline batteries for the Handheld Unit 8 replacement screws for the terminal lugs of the Base Unit 1 Instruction Sheet For technical support related to the operation of this device please contact: Siemens Energy & Automation, Inc. 3333 Old Milton Parkway Alpharetta, GA 30005 1-800-964-4114...
See Figures 1 & 2 Turn “OFF” and lock out the power to the equipment in which the Intelli-Arc Diagnostic Tool is to be installed. Move the handle of the breaker on the circuit to be analyzed to the “OFF” position. This circuit breaker serves as the disconnect device tor the Intelli-Arc Diagnostic Tool.
Turn off and lock out power supplying the device before removing base unit. Restore all branch circuit connections. Close cover if testing is complete or return to step 1 of Installation Instructions to test another branch circuit. Always remove Intelli-Arc Diagnostic Tool and replace load center or panelboard cover before leaving the work site. LED Test Procedure Turn “OFF”...
LED Indications Three sets of LED indicators are provided on the handheld device for use in troubleshooting branch circuit issues. These three indications give information regarding current (“AMPS”), ground fault level (“GF”), and arc fault level (“AF”). Current (“AMPS”) The full scale current for this LED indication is 20+A. LED indicators do not increase by uniform intervals.
Technical Specification Operating ambient temperature: 5ºC – 40ºC (41ºF – 104 ºF) Maximum relative humidity: 80% for temperatures up to 31ºC (88ºF) decreasing linearly to 50% at 40ºC (104ºF) Environment: Indoor use at altitude up to 2000 m (6561 feet) Range of operating voltage: 108V –...