EXCEL 5000™ System Styled Cabinet
The EXCEL 5000™ System Styled Cabinet is constructed
from a separately ordered Rough-in Ring, Subpanel and Door.
See Fig. 1. The Cabinets are available in two sizes: small
sized and full-sized. These instructions describe how to install
the Ring and Subpanel. See form no. 95-7486, EXCEL
5000™ System Styled Cabinet Doors Installation Instructions
to install the Door.
Fig. 1. EXCEL 5000™ Styled System Cabinet (small-sized
® U.S. Registered Trademark
Copyright © 2001 Honeywell • All Rights Reserved
Rings and Subpanels
1. Refer to the job drawings for Cabinet locations and
2. Install the Ring on a vibration-free surface in a clean,
3. Ensure that the location is visible and accessible for
4. Verify that the Ring is square by making sure the diago
nal measurements are equal. If not equal, apply pres
sure to the corners of the longer diagonal measurement
to force the Ring back into the square.
— Ring must be square so that the Door and latch operate
— Do not install Subpanel, or Door on Ring until after
construction has been completed.
Fig. 2 and 3 show Ring dimensions and mounting hole
locations. Fig. 4 and 5 show conduit knockout locations and
sizes. Rings can be surface or semiflush mounted.
Rings may be mounted in both vertical and horizontal clusters
and are interconnected through corresponding knockouts (see
Fig. 6). Hinges allow doors to fully open even when rings are
Ensure that the conduit entering the Ring does not permit
condensation drainage into the internal circuitry. Where this is
a possibility, bend the conduit and drill a hole at the lowest
point in the conduit so that water drains out before reaching
For wire runs between Rings that are bolted together, remove
all necessary (present and future) conduit knockouts before
the Rings are bolted together and mounted. Also remove the
necessary 5/16 in. (8 mm) and 1/2 in. (13 mm) bolt-hole
95- 7487- 1