15v DC network power supply
0.24A Single Phase Supply
15V DC Regulated Output
Output is Short Circuit Proof
Enclosure is DIN Rail Mount with Circuit Breaker Profile
Simple Installation - DIN Rail mount facilitates installation.
All connection terminals are accessible without disassembly
1. Mount the device on a DIN rail inside an approved enclosure.
2. Connect a single phase 0.25A feed to the control circuit supply terminals. This device must be earthed.
3. Connect the two power conductors of data cables to the device. There are two common methods of doing this:
a) Method 1: Use a 2 core cable to connect between the DDNP1501 and the data cable connector on a device that is
connected to the network. Parallel connect the GND and +12V terminals on the DDNP1501 to the GND and +12V
terminals on the network device.
b) Method 2: Loop the network cable to the DDNP1501 and connect the Green pair to GND terminal and Orange pair to
+12V terminal. Ensure that the other conductors are looped through using a suitable terminal block.
Warning – This is a class A product. In a domestic environment
this product may cause radio interference in which case the user
may be required to take adequate measures.
Read Instructions – We recommend that you read this
Instruction Manual prior to commencement of installation.
Power Sources – This device should only be operated from the
type of supply specified on the front cover. This device must be
Output – The load on this device should not exceed the specified
capacity of 1.5A. This device should be fed via a HRC fuse or
Mounting Location – Install in a dry, well-ventilated location.
Controllers may emit some mechanical noise.
account when deciding the mounting location.
Data Cable – Use screened, stranded RS485 data cable with
three twisted pairs. Segregate from mains cables by 300mm
minimum. Connect devices in a 'daisy chain'. A data cable that is
connected to an energised device is live. Do not cut or terminate
live data cables.
To reduce the risk of fire or electric shock, do not expose
this device to rain or moisture. Do not energise unless the
front cover is in place.
This device must be earthed.
Installation, programming and maintenance must be
carried out by qualified personnel.
Take this into