OFF main power switches to the unit. Electric shock can cause personal injury. Please read and follow the wiring instructions precisely; miswiring may cause permanent damage to the product GE Measurement & Control 6860 Cortona Dr., Suite B Goleta, CA 93117 Basic Installation for Non-Display Units www.ge-mcs.com...
Ventostat Wiring Diagrams The Ventostat family of products has two basic configurations. One configuration provides three active outputs (CO , RH and temperature) and an independent thermistor. It has an output terminal block with pins #1, 2 and 3. The other configuration provides only CO outputs and an independent thermistor and has no terminal block with pins 1, 2, and 3 installed.
Sensing Duct CO Concentrations Accessory Enclosures Duct-Mounting the Enclosures Model T1508 Duct Mount Enclosure (Aspiration Box) Ventostat products can be installed inside the return air ductwork, if The T8100/T8200/T8300 units can be installed inside a Model 1508 needed. As an alternative, please consider the T8031 unit. When Duct Mount Enclosure.
5,592,147 / 6,255,653 / 6,250,133 / 6,285,290 Thermistor Accuracy Warranty Repairs ±1°C (15° to 35°C) GE Sensing will repair Telaire product that fails to meet the terms provided for in the Return and Warranty Policy Statement (See, http:// www.ge-mcs.com/en/services-and-support.html).Warranty period shall RH Sensing Element start from date of manufacture and be based on product category and type of equipment as specified in Table 1: Product Warranty Periods.