AC Smart Advanced Control Smart Quick Guide PQCSW320A0E Note • Please read this installation/use manual before installing the product. • Install the product with an expert installation engineer with proper qualifications. • Even after reading this manual, please store this manual...
AC Smart TABLE OF CONTENTS Safety precautions ......................4 Introduction of AC Smart....................7 AC Smart characteristics ....................7 AC Smart exterior ......................8 AC Smart component ......................9 AC Smart product specification ..................9 ABOUT AC SMART......................10 Logging on to AC Smart ....................10 AC Smart screen composition ..................11 About control/monitoring menu..................12 About schedule menu ......................16 About record menu ......................21...
Safety Precautions Safety Precautions To prevent injury to the user or other people and property damage, the following instructions must be followed. I Incorrect operation due to ignoring instruction will cause harm or damage. The seriousness is classified by the following indications. WARNING This symbol indicates the possibility of death or serious injury.
Safety Precautions While re-installing the Do not use the power cord Do not disjoint randomly or established product, notify near Flammable gas or repair and remodel the the service center or combustibles, such as product. establishment specialty gasoline, benzene, thinner, store etc.
Safety Precautions Do not put firearms near Do not put an electric heater Do not spill water inside product. or conductor near to the product. product. • It can cause fire. • It can cause fire and • It can cause electric electric shock.
Safety Precautions CAUTION I During usage Clean by soft hands Use touch screen with a Do not place any live part using a cleaning material pen that product offers. on the surface having like a soft cloth. water. • It can result in fire and •...
Introduction of AC Smart Introduction of AC Smart AC Smart is a central controller that can manage maximum of 64 air condition indoor units individually or as a group. Also when you connect the AC Smart expansion kit, you can expand up to 128 units. With AC Smart, you can monitor or operate the air conditioner and ventilator installed in each room of the building from a location such as the management office of a building or administrative office of a school.
Introduction of AC Smart Web server and E-mail notification function AC Smart provides a web server function for the administrator to control the air conditioner by accessing the AC Smart remotely through the network. Also it provides the E-mail notification function to notify the error to the administrator located remotely via E-mail.
Introduction of AC Smart AC Smart component The components of AC Smart are as follows inside the box. Open the box of AC Smart and check whether all components are included. AC Smart Power adapter Quick Guide & Manual CD Power cord AC Smart product specification The product specification of AC Smart is as follows.
About AC Smart About AC Smart This chapter describes how to log in to AC Smart and the functional menu of AC Smart. Logging on to AC Smart When you turn on the power of AC Smart, the following log in screen will be displayed. You can log in as installation expert, administrator and general user to AC Smart.
About AC Smart About AC Smart screen composition When you log in to AC Smart, the following screen will be displayed. AC Smart menu Function execution screen Message window Log out button AC Smart menu This displays the menu for the function provided by AC Smart. When you log in as the general user you can only select the ‘Control/Monitoring’...
About AC Smart About control/monitoring menu Control/Monitoring menu is the menu to easily manage various units (Indoor units, ventilator) in one unit that can be commonly controlled. You can monitor or control the status information from Control/Monitoring menu in Zone, Group or Unit. Control/Monitoring menu screen is composed as follows.
About AC Smart I Zone, group and unit status display Status display of zone, group and unit Control/Monitoring menu displays the status of Zone, Group or Unit (Indoor unit, ventilator) through the following icons. Icon Status Zone Group Indoor unit Ventilator Normal operation Alarm...
About AC Smart I Zone, group and unit monitoring and control Monitoring information display of zone and group There is the ‘Monitoring’ tab on the bottom of the Control/Monitoring menu. Monitoring tab displays the detail information of the selected Zone, Group or Unit. The monitoring information of the Zone or Group is differently displayed as the monitoring information of the Unit.
About AC Smart Zone, group unit control There is a ‘Control’ tab located at the bottom of the Control/Monitoring menu. You can directly control the Zone, Group or Unit from the Control tab. You can set the desired indoor temperature the from the Control tab and execute/stop the operation of the unit (Indoor unit, ventilator).
About AC Smart About schedule menu Schedule is the function to execute the operation at a preset time by setting the operation of the unit (Indoor unit and ventilator) beforehand. You can set the schedule of the unit in Group from the schedule menu.
About AC Smart Schedule setting example This chapter describes how to create the schedule group and weekly pattern and how to create the schedule assuming that you have installed AC Smart. Schedule group creation To set the schedule after installing AC Smart, you must first create a schedule group. Here we will describe an example where a group called ‘3rd floor’...
About AC Smart . Designate the group and press the ] and [ ] button to change the composition of the unit. At this time, assign ‘ac3_1’, ‘ac3_2’ and ‘ac3_3’ units to group named ‘3rd floor’. . Press the [Save] button to save the current setting.
About AC Smart . Designate the Group to set the schedule from ‘1. Select the weekly pattern’. Here, ‘Summer’ is designated as weekly pattern.. . Designate the time and operation of the event from ‘2. Add event’. You can use the control command or apply the daily pattern to the applicable dates for the operation.
About AC Smart Schedule creation When you have created the schedule group and weekly pattern, lastly you must set the period to apply using based on the group and weekly pattern. Here we will describe an example of completing the schedule setting using the schedule group, ‘3rd floor’, and weekly pattern, ‘Summer’. .
About AC Smart About record menu When there is a change in status of the unit (Indoor unit and ventilator) interfacing with AC Smart through the network or in set status of AC Smart, AC Smart records the applicable information. You can categorize or view the change records by type or period from the record menu.
About AC Smart About automatic control menu You can automatically control the indoor unit and ventilator interfacing with AC Smart according to the temperature and time. Automatic control menu provides the following 3 functions. • Temperature limit operation: Function to set the upper and lower temperature and maintain the indoor temperature within the set temperature range •...
About AC Smart I Temperature limit operation Temperature limit operation is the function to maintain the indoor temperature within a certain range. When you set the upper temperature, lower temperature and temperature criteria in the temperature limit operation, you can operate the stopped indoor unit in cool mode or heat mode depending on the indoor temperature.
About AC Smart Temperature limit condition setting When you press the [Condition setting] button, the ‘Condition setting’ screen to set the Temperature limit operation function and related items will be displayed as shown in the left picture. Designate the Temperature limit operation group and set the item for Temperature limit operation, and then press the [Save] button to set the Temperature limit operation function to the applicable group.
About AC Smart I Automatic switch operation Automatic switch operation is the function to automatically switch the operating mode (Cool/Heat) of the air conditioner according to set temperature and range. That is, when the current temperature is more than lower than the set temperature range base don the criteria, it will operate the Heat mode to maintain the temperature within the set range.
About AC Smart Automatic switch operation condition setting When you press the [Condition setting] button, the ‘Condition setting’ screen to set the Automatic switch operation function and related items will be displayed as shown in the left picture. Designate the Automatic switch operation group and set the item for Automatic switch operation, and then press the [Save] button to set the Automatic switch operation function to the applicable group.
About AC Smart I Time limit operation Time limit operation is the function to limit the using time of the indoor unit and ventilator individually by the user. When the indoor unit and ventilator operate for more than the time set for the day in Time limit operation, the operation will automatically stop.
About AC Smart Edit time limit operation group When you press the [Edit group] button, ‘Edit group’ screen to create, edit or delete the group for Time limit operation is displayed as shown on the left picture. In the ‘Group’, you can add a new group or delete/rename the existing group.
About AC Smart About system setting menu You can conveniently manage the units (Indoor unit and ventilator) with AC Smart according to the installed location or functional characteristics in Zone or Group. The system setting menu provides function to include or exclude these indoor units or ventilators to or from the Group or Zone according to the physical structure and logical structure.
About AC Smart Unit management (Unit registration, On/Off device registration, control interface setting) When you click on the [Unit management] button located below the system setting menu, the following ‘Unit management’ screen’ will be displayed. In the unit management menu, you can register a newly connected unit or edit/delete the unit of an existing Zone.
About AC Smart About environment setting menu Environment setting menu provides function to set the necessary password and network to use AC smart as well as the screen adjustment function and screen saver function for user convenience. Environment setting menu is composed of 9 sub menus as shown below in the picture. But for network, E-mail setting, S/W upgrade and DB management menu, you must log in as the installation expert mode for the setting.
About AC Smart About web server function AC Smart provides the web server function so that the user can connect to AC Smart remotely through the network. The administrator can monitor and control the air conditioner from a remote location through this function. To use the web server function, you must set the network information to AC Smart.