Controller operation-Function settings
This control starts heating operation when the control object group is stopped and the room temperature
drops below the preset lower limit temperature. Also, this control starts cooling operation when
the control object group is stopped and the room temperature rises above the preset upper limit
The Night setback function is not available if the operation and the temperature setting are performed
from the remote controller.
If the room temperature is measured by the air-conditioner's suction temperature sensor, the accurate
temperature may not be obtained when the air-conditioner is inactive or when the air is not clean. In
this case, switch the sensor to a remote sensor (PAC-SE40TSA/PAC-SE41TS-E) or a remote control
Night setback Yes
Select "Night setback" from the Main menu (refer
to page 18), and press the SELECT button.
The current settings will appear.
Press the SELECT button to go to the setting