GULA Gas Fired Warm Air Furnace User’s Information Manual WARNING If the information in these instructions is not followed exactly, a fire or explosion may result causing property damage, personal injury or loss of life. – Do not store or use gasoline or other flammable vapors and liquids in the vicinity of this or any other appliance.
Contents Important Note To The Owner ................3 Component Identification ..............4 General Information ................5 Unit Location ..................... 5 Unit Installation ....................5 Clearances and Accessibility ................6 Air Requirements ....................6 Combustion Air (Non-Direct Vent/Single Pipe) ........... 6 Flue Pipe and Condensate Drainage ..............
WARNING Should overheating occur, or the gas supply fail to shut off, shut off the manual gas valve to the furnace before shutting off the electrical supply. WARNING To avoid death, personal injury or property damage, do not use this furnace if any part of the furnace has been under water. Immediately call a qualified service technician to inspect the furnace and to replace any part of the control system and any gas control having been under water.
Component Identification Upflow /Horizontal (GULA Models) Gas Valve Coil Front Cover Pressure Tap Gas Line Entrance (Alternate) Coil Front Cover Drain Port Pressure Switch Drain Line Penetrations Gas Manifold Drain Trap Hot Surface Igniter Blower Door Interlock Switch Rollout Limit...
General Information This furnace is built to provide many years of safe and dependable service, providing it is properly installed and main- tained. However, abuse and/or improper use can shorten the life of the furnace and create hazards for you, the home- owner.
General Information Clearances and Accessibility Carbon monoxide or “CO” is a colorless and odorless gas Installations must adhere to the clearances to combustible produced when fuel is not burned completely or when the materials for which this furnace has been design certified. flame does not receive sufficient oxygen.
To prevent possible death or personal injury due to The colder the air; the less moisture it can hold. As air is asphyxiation, Amana Condensing Gas Fired Warm warmed, its ability to hold moisture is increased. Air Furnaces must be Category IV vented.
General Information For Propane (LP) Gas Installations Only For furnaces operating on propane gas, please review the following warnings before use. WARNING To avoid death, personal injury or property damage due to explosion or fire, install a gas detecting warning device. Since the odorant in propane gas can be reduced by iron oxide (rust), a gas detecting warning device is the only reliable method to detect propane gas leaks.
Operating Your Furnace Furnace Operation In the heating mode, gas is burned and the products of WARNING combustion are drawn through a heat exchanger by an induced draft blower. The flue gases are then exhausted from your home through a flue pipe system. The Electrical components are contained in both furnace’s circulator blower passes indoor air over the compartments.
Operating Your Furnace Starting Your Furnace Gas Valve On/Off To put your furnace into operation, follow the steps listed Selector below. Inlet Pressure Switch 1. Close the external manual gas shut-off valve. 2. Turn off the electrical power to the furnace. 3.
Safety Circuits A number of safety circuits are employed to ensure safe and proper furnace operation. These circuits serve to control any potential safety hazards and, as inputs in the monitoring and diagnosis of abnormal function. These circuits are continuously monitored by the integrated control module. Integrated Control Module ROLLOUT PRIMARY LIMIT...
Routine Maintenance If you perform maintenance on the furnace yourself, remember that certain mechanical and electrical knowledge, skills and tools are required to perform maintenance on the furnace. Personal injury or death my result. If you are not properly trained. You should call your installing dealer or place of purchase if you are uncertain about your ability to perform maintenance.
Routine Maintenance Filters Filters must be inspected, cleaned or changed every two months or as required. As a homeowner, it is your personal responsibility to keep air filters clean. Remember that dirty filters are the most common cause of inadequate heating or cooling performance.
Troubleshooting / Before You Request a Service Call If your furnace is not operating or is performing improperly, take time to perform the following checks before requesting service. A couple of simple checks may allow you to avoid a service call. If the following steps do not resolve the problem, contact a qualified servicer for further troubleshooting and/or repairs.
Safety Labels NOTE: If safety labels are missing or illegible, contact the installing dealer or our Customer Service Department for ordering information. WARNING: IMPROPER INSTALLATION, ADJUSTMENT, ALTER- AVERTISSEMENT: UNE INSTALLATION, UN REGLAGE, ATION, SERVICE OR MAINTAINANCE CAN CAUSE PROPERTY UNE MODIFICATION, UNE ENTRETIEN, OU UNE DAMAGE, PERSONAL INJURY OR LOSS OF LIFE, EXPOSURE MAINTAINANCE INCORRECTS PEUVENT ENTRAINER DES TO SUSTANCES IN FUEL OR FROM FUEL COMBUSTION WHICH...
For Additional Information Most questions can be answered by your local Amana dealer. If you need further information regarding the operation, maintenance, or service of your furnace, contact your dealer. If you have other matters that cannot be resolved locally, or you need additional information regarding other heating...
® is a trademark of Maytag Worldwide N.V. and is used under license to Goodman Company, L.P. All rights reserved.