Wiring must comply with applicable codes, ordinances, and regulations.
CAUTION: Voltage Hazard.
Can cause electrical shock or equipment damage. Disconnect power before beginning installation.
Wire entire panel before applying transformer power.
Install thermostats using instructions provided with thermostats.
Connect thermostat to zone panel. To connect wire to the panel, strip
approximately 1/4 in. of insulation and push wire into terminal. To
release wire, press the button on top of the terminal. In retrofit applica-
tions, trim end of wire if not straight.
If the thermostat has separate E and Aux terminals, install a jumper
between the two terminals.
Wires can be run behind the panel, through
wire channels on the panel's sides, and
must be attached to a wiring anchor with a
Install dampers using instructions provided
with dampers. Connect dampers to zone
NOTE: Multiple dampers can be wired in
Connect DATS as shown.
ARD OR ZD DAMPER
ARD OR ZD DAMPER SPRING-OPEN POWER-CLOSED
ZONE 2 THERMOSTAT
RRD OR MARD DAMPER