29 percent of the energy used to heat a controlled zone. • Offers up to a 12 percent energy saving during comfort periods compared with conventional bi- metallic electric heating thermostat, according to the Electric Power Research Institute.
Welcome ... to the world of comfort and energy savings with your new Honeywell programmable thermostat. Your new T4700 Chronotherm™ Programmable Electronic Line Voltage Thermostat is designed to provide you with reliable, precise temperature control. When you follow the simple programming...
Specifications Models: T4700A: SPST; makes heating circuit on temperature fall. T4700B: DPST; makes heating circuit on temperature fall. Breaks both sides of 240 volt line with switch in OFF position. Temperature Ratings: Operating Range: -20 to +104°F (-30° to +40°C). Control Range: 45 to 80°F (7 to 27°C) in 1°...
Programming Thermostat Initial Powerup When the thermostat is first powered up (or after eight hours of continuous power loss), the display blinks for two seconds and then undergoes a self-test — while 00E displays for about 15 seconds. This is followed by the display flashing (1:00 PM);...
(Table 1) by inserting a bent paper clip or similar wire into the small hole on the front of the thermostat (next to to the (+) key with the cover open). This resets only the clock; the programmed schedule is retained.
Table 2. Setting the Current Day and Time. Step Press This Key Display Shows Displays day of the week. Displays changed day of the week. Displays hour of the day. Displays changed hour of the day. Displays minute of the day. Displays changed minute of the day.
Table 3. Setting the Daily Schedule (7-Days). Step Press This Key NOTE: Continue through LEAVE, RETURN, and SLEEP periods using the same procedure to set the time and temperature for each period. To easily copy one day schedule to another day, see Table 4. 69-1396—2 Display Shows Scrolling through the display shows...
Table 4. Copying Schedules to Another Day. Step Press This Key NOTE: To exit the programming mode: 1) press and hold the Prog key for three seconds and the display returns to Run mode, or 2) during the programming session, after five minutes elapsed time with no program change, the display reverts to Run mode.
Step Press This Key Temporarily Overriding a Program Temporary (TEMP) Mode Indefinitely Overriding a Program Hold (HOLD) Mode Programming Additional Functions To change display or function (for example, 69-1396—2 Table 5. Overriding a Program. Display Shows Changes to TEMPorary mode and controls at a new temperature until the next scheduled event (for example, RETURN).
Table 6. Programming Additional Functions. Function Press This Key Begin sequence to convert display or mode. Convert to °C or °F. Convert 5-1-1 to 7 day. NOTE: To exit the programming mode: 1) press and hold the Prog key for three seconds and the display returns to Run mode, or 2) during the programming session, after five minutes elapsed time with no program change, the display reverts to Run mode.
3800W. Push Reset key to clear and reset clock. Push Reset key to clear and reset clock. Push Reset key to clear and reset clock. If problem persists, call Honeywell Customer Response Center at 1-800-468-1502. Press the (+) key until the setpoint displayed exceeds the room temper- ature to verify that the thermostat is turning on the baseboard heater.
Customer Assistance Please direct any questions about the operation of this thermostat to Honeywell Customer Assistance at 1-800-468-1502, Monday-Friday, 7:00 a.m. - 5:30 p.m. Central time. 69-1396—2...
This warranty does not cover removal or reinstallation costs. This warranty shall not apply if it is shown by Honeywell that the defect or malfunction was caused by damage which occurred while the product was in the possession of a consumer.
If you have any questions concerning this warranty, please write Honeywell Customer Assistance Center, 1985 Douglas Dr, Golden Valley, MN 55422 or call 1-800-468-1502, Monday-Friday, 7:00 a.m. to 5:30 p.m., Central time. In Canada, write Retail Products ON15-02H, Honeywell Limited/ Honeywell Limitée, 35 Dynamic Drive, Scarborough, Ontario M1V4Z9.
Automation and Control Solutions Honeywell International Inc. 1985 Douglas Drive North Golden Valley, MN 55422 69-1396—2 G.H. Rev. 1-03 Honeywell Limited-Honeywell Limitée 35 Dynamic Drive Scarborough, Ontario M1V 4Z9 Printed in U.S.A. on recycled paper containing at least 10% post-consumer paper fibers.