WINDOW TYPE WINDOW TYPE WINDOW TYPE WINDOW TYPE WINDOW TYPE WINDOW TYPE WINDOW TYPE WINDOW TYPE WINDOW TYPE WINDOW TYPE AIR CONDITIONER AIR CONDITIONER AIR CONDITIONER AIR CONDITIONER AIR CONDITIONER AIR CONDITIONER AIR CONDITIONER AIR CONDITIONER AIR CONDITIONER AIR CONDITIONER...
CONTENTS 1. ELECTRICAL SAFETY RULES..............1 2. UNIT PARTS IDENTIFICATION..............2 3. POINTS FOR ATTENTION WHEN OPERATING........3 4. OPERATION PANEL .............4 (Cooling only type) OPERATION INSTRUCTION..............4 5. CARE AND MAINTENANCE..............7 6. WINDOW INSTALLATION INSTRUCTIONS.........10 7. TROUBLESHOOTING TIPS..............15...
ELECTRICAL SAFETY RULES CAUTION CAUTION All wiring must comply with local and national electrical codes and be installed by a qualified electrician. If you have any questions regarding the following instructions, contact a qualified electrician. Never insert your fingers or any foreign objects into the air outlet. Take special care to warn children of these dangers.
3. Before turning on the unit, make sure that the air inlet grille and air outlet grille are not obstructed by anything. 4. This air conditioner is designed to be operated under conditions as follows: Outdoor temp. : 18-43 C Indoor temp. : 21-32 C...
OPERATION PANEL(Cooling only type) THERMOSTAT SELECTOR HIGH HIGH COOL COOL COOL WAIT THREE MINUTES BEFORE RESTARTING Fig. 2 OPERATION INSTRUCTION OPERATION PANEL 1. Pull the top of the operation cover to open it. 2. Close the operation cover and press the top until it snaps into the locked position.
Do not change the operation mode between "LOW COOL" and "HIGH COOL" too often. THERMOSTAT The thermostat automatically starts and stops the THERMOSTAT running of the compressor in the air conditioner in order to control maintain comfortable room temperature.
Note During the cooling operation of the unit, when the thermostat knob is rotated counterclockwise, allow at least three minutes before turning back the knob to the "COOLER" direction. Otherwise the fuse may blow due to an overload of the unit. MANUAL LOUVER Horizontal air flow adjustment (manually) Move the "T"...
Never attempt to clean the unit by or any other chemicals, or any liquid pouring water directly over any of the insecticide on the air conditioner, as surface areas, as this will cause these substances may cause flaking deterioration of electrical components off of the paint, cracking or deformation and wiring insulation.
CLEANING THE AIR FILTER If the air filter becomes clogged with dust, air flow is obstructed and reduces cooling efficiency. The air filter should be cleaned every two weeks. Push Here Fig. 7 1. Removal of Air Filter 1) Press "PUSH" on the bottom corners of the inlet grill. See Fig. 7 2) Pull the air filter down to remove.
FRONT PANEL Dust may accumulate on the front panel, use soft wet cloth with a neutral cleaning agent to wipe it. Never use water over 50 C, alcohol, gasoline, acid, solvent or brush to clean the front panel as this will damage the surface of the part. End-of Season Care In-Season Care OPERATING THE...
WINDOW INSTALLATION INSTRUCTIONS Parts Insluded 5. Window sash seat 6. Top mounting rail seal strip 7. Foam top window gasket 4. Top mounting rail 3. Accordion panel 13. Connection bar 1. Sill support 2. Bottom mounting rail 8. Type A (4) 9.
Attach securely with nails or screws provided by the installer. Remove the Air conditioner From the Case 1. Removal of Air Filter A. Press "PUSH" on the bottom corners of the inlet grill.
C. Remove the 2 screws on each side of the case. Keep these for later use. D. Slide the air conditioner from the case by Fig. 11 gripping the base pan handle and pulling forward while bracing the case.
D. Install the Accordion panels Attach the two Connection Bar to Connect the shutter with the Connection the case. Bar. Shutter Connection Bar Fig. 18 Fig. 19 Insert the shutters into its frame bar. Clip the shutters onto the frame bars And install the upper and lower frame with the clips.
D. Loosely assemble the sill supports. Indoor Outdoor Sill support Bolt Fig. 23 E. Select the position that will place the sill Frame guide supports near the outermost point on the sill. Attach the sill supports to the case 1/3" Maximum track hole in relation to the selected position using 4 type C screws in each...
Save time and money! Review the chart below first and you may not need to call for service. Problem Possible Causes What To Do The air conditioner is Make sure the air conditioner plug is pushed Air conditioner unplugged. completely into the outlet. does not start The fuse is blown/circuit Check the house fuse/circuit breaker box and breaker is tripped.
Clean the filter at least every 30 days. See the Operating Instructions section. The room may have been When the air conditioner is first turned on you hot. need to allow time for the room to cool down. Cold air is escaping.