Arrangement of piping directions Cushion Rear left Rear Left right Pipe supporting plate Right Below The marks from in the figure are the parts numbers. The distance between the indoor unit and the floor should be more than 2m. No.0010515136...
Before inserting power plug into receptacle, check the voltage without fail. The power source is the same as the corresponding name plate. Install an exclusive branch circuit of the power. A receptacle shall be set up in a distance where the power cable can be reached. Do not extend the cable by cutting it. Selection of pipe...
In case of left side piping, cut away, with a nipper, the lid for left piping. In case of left-rear piping, bend the pipes according to the piping direction to the mark of hole for left-rear piping which is marked on heat insulation materials.
Indoor unit 1. Insert the drain hose into the dent of heat insulation materials of indoor unit. 2. Insert the indoor/outdoor electric cable from backside of indoor unit, and pull it out on the front side, then connect them. 3. Coat the flaring seal face with refrigerant oil and connect pipes.
Be careful that matters, such as wastes of sands, etc. shall not enter the pipe. 3.Connection Use the same method on indoor unit. Loosen the screws on terminal block and insert the plugs fully into terminal block, then tighten the screws.
Brand new outdoor unit is charged 50g or 80g(22k) more refrigerant than regulated weight. Only for first installation, this extra 50g or 80g(22k) can be used to purge air in pipes. During this procedure, 50g or 80g(22k) refrigerant will be discharged in piping.
Please pour water in the drain pan of the indoor unit, and confirm that drainage is carried out surely to outdoor. In case that the attached drain hose is in a room, please apply heat insulation to it without fail.