AXPTC125 POWER TEE SPLICE CONNECTION KIT
ENCLOSURE WITH TERMINAL BLOCKS
CABLE TIE (not shown)
STOPPING PLUG AND LOCKNUT
GUIDE TUBES (not shown)
PRODUCT LABEL (not shown)
Pipe Clamp – PC03, PC12 or PC20 (included)
Fiberglass Tape – GT6 or GT60
OPTIONAL INSTALLATION MATERIAL
HC-SPA Small Pipe Adapter – For 1.0"
(25 mm) diameter pipe and below.
Adjustable Wrench (52mm [2.1"] size)
Needle Nose Pliers
Small Flat Blade Screwdriver
Large Slotted Screwdriver
Allen wrench (10mm [3/8"] size)
TULSA, OK 74146
The AXPTC125 Power Tee Splice Connection Kit is
designed to connect three heater cables in a tee splice
configuration and with the removable plug can also connect
the heating cables to customer supplied power wiring. This
kit is designed for use with all wattages of Nelson Heat Trace
CLT-J(ordinary locations), CLT-JT(ordinary locations), LT-J,
LT-JT, UT-1, QLT-J, HLT-J and XLT-J heater cables. The
AXPTC125 is rated IP66/NEMA 4X. The AXPTC125
connection kit may be used to connect multiple heater
segments, connect different wattage cables together or to
provide access to serviceable equipment.
These instructions are to be used together with the
installation and maintenance instructions for self-regulating
heater cable (GA-1765).
GA-5052 Rev. 3
Sheet 1 of 10