This manual contains text, diagrams and explanations which will guide the reader in the correct installation
and operation of the FX
attempting to install or use the unit.
Further information can be found in the FX SERIES PROGRAMMING MANUAL(ΙΙ), FX
Programming Manual, FX
HARDWARE MANUAL of each PLC.
Compliance with EC directive (CE Marking)
This note does not guarantee that an entire mechanical module produced in accordance with the contents
of this note will comply with the following standards.
Compliance to EMC directive and LVD directive for the entire mechanical module should be checked by
the user/manufacturer. For more information please consult with your nearest Mitsubishi product provider.
Regarding the standards that comply with the main unit, please refer to either the FX series product
catalog or consult with your nearest Mitsubishi product provider.
Requirement for Compliance with EMC directive
The following products have shown compliance through direct testing (of the identified standards below)
and design analysis (through the creation of a technical construction file) to the European Directive for
Electromagnetic Compatibility (2014/30/EU) when used as directed by the appropriate documentation.
This product is designed for use in industrial applications.
Programmable Controller (Open Type Equipment)
from December 1st, 1998 FX
- Equipment requirements and tests
Caution for EC Directive
-2DA have been found to be compliant to the European standards in the aforesaid manual and
directive. However, for the very best performance from what are in fact delicate measuring and controlled
output device Mitsubishi Electric would like to make the following points;
As analog devices are sensitive by nature, their use should be considered carefully.
For users of proprietary cables (integral with sensors or actuators), these users should follow those
manufacturers installation requirements.
Mitsubishi Electric recommend that shielded cables should be used. If NO other EMC protection is
provided, then users may experience temporary loss or accuracy between ±10% in very heavy industrial
However, Mitsubishi Electric suggest that if adequate EMC precautions are followed for the users
complete control system, users should expect accuracy as specified in this manual.
Sensitive analog cable should not be laid in the same trunking or cable conduit as high voltage
cabling. Where possible users should run analog cables separately.
Good cable shielding should be used. When terminating the shield at Earth - ensure that no earth
loops are accidentally created.
-2DA special function block and should be read and understood before
Compliance with all relevant aspects of the standard.
• Radiated Emission
• Conducted Emission
• Radiated electromagnetic field
• Fast transient burst
• Electrostatic discharge
• High-energy surge
• Voltage drops and interruptions
• Conducted RF
• Power frequency magnetic field
-2DA SPECIAL FUNCTION BLOCK