DELUXE HIGH WALL MINI SPLIT INSTALLATION INSTRUCTIONS IMPORTANT! Please read this instruction sheet completely before installing the product. This air conditioning system meets strict safety and operating standards. As the installer or service person, it is an important part of your job to install or service the system so it operates safely and efficiently.
INSTALLATION OVERVIEW Installation Required Parts Required Tools Requirements The following should be always observed for safety ....3 Installation of indoor, outdoor Installation guide map Level gauge unit ..........4 Four type "A" screws & plastic Screw driver anchors Electric drill Connecting cable Hole core drill Ø50mm(1.97") Horizontal meter...
THE FOLLOWING SHOULD BE ALWAYS OBSERVED FOR SAFETY Be sure to read "THE FOLLOWING SHOULD BE ALWAYS OBSERVED FOR SAFETY" before installing the air conditioner. Be sure to observe the cautions specified here as they include important items related to safety. The indications and meanings are as follows.
INSTALLATION OF INDOOR, OUTDOOR UNIT Read completely, then follow step by step. Select the best location Rooftop Installations: If the outdoor unit is installed on a roof structure, be sure to level the unit. Ensure the roof structure and Indoor unit anchoring method are adequate for the unit location.
Preparing work for Installation Cover pipe and cover side remove Open panel front Remove two screws(for fixing cover pipe) Pull up the cover side of desired connecting First,Pull the grille bottom, then remove direction, then cover side is separated. screws(2 pieces), and close grille bottom In case connecting direction is left or right, path again.
Sticking the installation guide map and fixing Indoor unit Look at suited horizon by horizontal Put an Installation Guide Map meter on the horizontal setting line, on the desired surface. and Fix lightly the map by adhesive INSTALLATION GUIDE MAP tape.
FLARING WORK AND CONNECTION OF PIPING Flaring work Main cause for gas leakage is due to defect in Handle flaring work. Carry out correct flaring work in the following procedure. Yoke Cut the pipes and the cable. Cone Use the piping kit accessory or the pipes purchased locally.
Tape the tubing, drain hose and the connecting When extending the drain hose at the indoor unit, cable. Be sure that the drain hose is located at install the drain pipe. the lowest side of the bundle. Locating at the upper side can cause drain pan to overflow inside the unit.
Connection of the CAUTION Installation Information (For right piping) pipes-Outdoor • Good case For right piping, follow the instruction below. Press on the upper side of clamp and Align the center of the pipings and unfold the tubing to downward slowly. sufficiently tighten the flare nut by hand.
CONNECTING THE CABLE BETWEEN INDOOR UNIT AND OUTDOOR UNIT Connection of the cable 1. Remove the cover control from the unit by loosening the 3 screws. Wiring Diagram 2. Dismount caps on the conduit panel. Connecting cable(Low voltage) b Indoor Unit Outdoor Unit 3.
Connection method of the connecting cable(Example) (1) Dismount two-caps on the conduit panel. (2) Make a hole appropriate for the passage of connection cable through on cap by tool. (for low voltage line) (3) Pass the connecting cable through the hole. Terminal (4) Properly connect the cable on the terminal block.
CHECKING THE DRAINAGE AND FORMING THE PIPINGS Form the piping Checking the drainage Form the piping by wrapping the connecting portion of the indoor unit with To check the drainage. insulation material and secure it with two kinds of vinyl tapes. Pour a glass of water on the evaporator.
CAUTION CAUTION If a power plug is not to be used, provide a circuit breaker between power source and the unit as shown below. Main power source Circuit Breaker Conditioner Use a circuit breaker or time delay fuse. Connect the cable to the indoor unit 1.
AIR PURGING Air purging Do a leak test of all joints of the tubing(both indoor and outdoor) and both gas and liquid side service valves. Air and moisture remaining in the refrigerant Bubbles indicate a leak. Be sure to wipe off the system have undesirable effects as indicated soap with a clean cloth.
Soap water method Liquid side (1) Remove the caps from the 2-way and 3-way valves. (2) Remove the service-port cap from the 3-way valve. (3) To open the 2-way valve turn the valve stem Gas side counterclockwise approximately 90°, wait for 2-way valve about 2~3 sec, and close it.
PANEL FRONT ASSEMBLY First, Check the side cover assembly exactly, Drive two screws. Fix power cord in the bottom groove of cover side left. Assemble connecting lead wire with controller and first fix the upper part of panel front, then match the lower part of panel front Panel Front Connector...
TEST RUNNING 1. Check that all tubing and wiring have been 3. Ensure the difference between the intake properly connected. temperature and the discharge is more than 8°C 2. Check that the gas and liquid side service valves (46°F) are fully open. Intake temperature Discharge air Prepare remote control...