Instructions relating to heating (*) are applicable only to "HEAT & COOL MODEL" (Reverse Cycle).
Before requesting service, perform the following checks:
Doesn't operate immedi-
Noise is heard:
Mist or steam are
Airflow is weak or stops:
Water is produced from
the outdoor unit:
In the event of a malfunction (burning smell, etc.), immediately stop operation, turn off the elec-
trical breaker, and consult authorized service personnel.
Merely turning off the unit's power switch will not completely disconnect the unit from the power
source. Always be sure to turn off the electrical breaker to ensure that power is completely off.
G If the unit is stopped and then immediately started again, the com-
pressor will not operate for about 3 minutes, in order to prevent
G Whenever the power switch is turned off then on again, the pro-
tection circuit will operate for about 3 minutes, preventing unit
operation during that period.
G During operation and immediately after stopping the unit, the
sound of water flowing in the air conditioner's piping may be
heard. Also, noise may be particularly noticeable for about 2 to 3
minutes after starting operation (sound of coolant flowing).
G During operation, a slight squeaking sound may be heard. This is
the result of minute expansion and contraction of the front cover
due to temperature changes.
*G During Heating operation, a sizzling sound may be heard occa-
sional. This sound is produced by the Automatic Defrosting op-
G Some smell may be emitted from the indoor unit. This smell is
the result of room smells (furniture, tobacco, etc.) which have
been taken into the air conditioner.
G During Cooling or Dry operation, a thin mist may be seen emitted
from the indoor unit. This results from the sudden Cooling of
room air by the air emitted from the air conditioner, resulting in
condensation and misting.
*G During Heating operation, the outdoor unit's fan may stop, and
steam may be seen rising from the unit. This is due to Automatic
*G When Heating operation is started, fan speed is temporarily very
low, to allow internal parts to warm up.
*G During Heating operation, if the room temperature rises above
the thermostat setting, the outdoor unit will stop, and the indoor
unit will operate at very low fan speed. If you wish to warm the
room further, set the thermostat for a higher setting.
*G During Heating operation, the unit will temporarily stop opera-
tion (between 7 and 15 minutes) as the Automatic Defrosting mode
operates. During Automatic Defrosting operation, the OPERATION
indicator lamp will flash.
G The fan may operate at very low speed during Dry operation or
when the unit is monitoring the room's temperature.
G In the monitor AUTO operation, the fan will operate at very low
*G During Heating operation, water may be produced from the out-
door unit due to Automatic Defrosting operation.