On an annual basis, maintenance is required to ensure TrueDRY runs at peak efficiency.
Unplug TrueDRY DH65 before beginning ser-
vice. Grip and remove thumb screws (4 per
collar) and slide collars off.
Using a 1/2-in. hex drive or standard screw-
driver, remove the eight screws on either
side of the TrueDRY DH65. The side and
top panels can then be removed. Using a
damp cloth, wipe excess dust and debris
from blower, refrigerant coils, and compres-
sor coils. Reattach panels and collars when
Grip filter tab at bottom to remove.
Replace with new filter.
Check the drain connection and drain line
to ensure it is clear of debris and sludge.
Ensure all hose connections are secure once
maintenance of the drain lines is complete.
When service is complete, initiate a call for
dehumidification and check that the com-
pressor and fan activate. If using the digital
VisionPRO IAQ or TrueIAQ controls, reset
9/22/2008 10:02:41 AM