SPLIT AIR CONDITIONER OPERATION MANUAL AS102AMARA AU102ACARA (HSU-10HA03(DB)) AS102ALARA AU102ACARA (HSU-10H03(DB)) AS122AYARA AU122ACARA (HSU-12HA03(DB)) AS122AVARA AU122ACARA (HSU-12H03(DB)) Digital DC Variable Frequency Healthy Split Air Conditioner Please read this manual carefully before use. Please keep this manual carefully and safely. No.0010540438...
Consult your local authorities for the name inoperative and safe. Unplug the air and address of the waste materials conditioner in order to avoid the risk of child collecting centers and waste paper diposal entrapment. services nearest to your house.
The refrigerating circuit is leak-proof. How is the connector insulated? accordance with specifications. Is the electric connection between the indoor and outdoor units firmly inserted into the The machine is adaptive in following situation terminal plate? 1.Applicable ambient temperature range:...
Manual Button connection wire to ensure it be clamped tightly. This button is only used for test refrigerating operation when the room temperature is below 16 , so it should not be used in normal situation. 8. Emergency Manual Button 3.
(2) Unscrew by 1/2 cycle the nut on the mouth of the thick pipe connected with the three-way valve difference between the indoor temperature and set temperature. with a spanner.
Fix the outdoor support on the wall with M10 expansion screws, then screw tightly the outdoor temperature is close to the set temperature. In heating unit on the support with M10 bolts and nuts, and leveled. If it is installed on wall or roof, the stand mode, when the room temperature is the set temperature, shall be firmly fixed to resist the earthquake or strong wind.
Fix the mounting plate on a smooth wall surface under the beam or beside a column. First fix the mounting plate with a steel nail,then level it with a level meter or a drop line, then fix it with A4 50 cement nails.If the expansion screws are used,first drill holes into the wall( 4.8mm), then...
When electronic-started type fluorescent lamp or change-over type fluorescent lamp or Install the indoor unit where its cold air and hot air can be easily sent to all the corners of the room. wireless telephone is installed in the room, the receiver is apt to be disturbed in receiving the Install the indoor unit where the power socket is near and there is sufficient space around the indoor unit.
The step 4 and step 5 above can be adjusted according to the practical situation. This procedure is a reference to the installation person and customer, it can be adjusted according to the practical situation.
Press mode button, For each press, mode changes as follows: make the air conditioner be grounded through the power supply socket. If the power supply wire is damaged, it must be replaced by the manufacturer or its service center or TEMP professional person.
Turn off 4 50 Press ON/OFF button to turn off the unit; all the displays disappear from LCD and all the lamps on indoor unit go out. And the swing louvers will all be closed automatically. Notes: After turning off, the unit must not be restarted until 3 minutes later to protect the system.
With the time set function, the air conditioner can be turned on and off automatically at your set time. You can let your air conditioner be turned on or off automatically after you wake up in the morning, Mounting Plate before you come back from work in the evening, or after you fall asleep at night.
When a power failure suddenly occurs during the air conditioner is working after the power failure Fuse or circuit breaker often breaks; resume is set, if the air conditioner will not be used for a long time, please cut off the power supply to Water is leaked during cooling and dehumidifying;...
Trouble Shooting Operation Emergency Operation & Test Operation When your remote controller is lost or cannot be used, the unit can be operated with a Air does not blow or the fan speed cannot be During the dehumidifying operation, when the function of emergency operation.
It is a watery fog formed and other failures would also occur. by a condensed air blew out of the unit.
Maintenance after Season of Use Do not spray any paint or insecticide on the air Turn on the machine and let it operate for half a day under the status of sending air in Conditioner. a sunny day so as to make the inside of the air conditioner fully dry.
>40 The multiple light catalysis air filter shall be put in sunshine once every half a year (8 hours each time), while the air filter without the light catalysis shall be replaced every half a year, which can...