Installation Manual of Room Air Conditioner Necessary Tools for Installation 1.Driver 2.Hacksaw 3.Hole core drill 4.Spanner(17,19 and 26mm) Accessory parts Number Accessory parts articles Remote controller Mark R-03 dry battery Mounting plate Drain hose 4X25 Plastic cap Screw Drain-elbow Cushion...
106.5 Floor fixing dimensions of the outdoor unit (Unit:mm) Fixing of outdoor unit Selection of Installation Place Indoor Unit Place, robust not causing vibration, where the body can be supported sufficiently. Place, not affected by heat or steam generated in the vicinity, where inlet and outlet of the unit are not disturbed.
Indoor unit 1.Fitting of the Mounting Plate and Positioning of the wall Hole When the mounting plate is first fixed 1.Carry out, based on the neighboring pillars or lintels, a proper leveling for the plate to be fixed against the wall, then temporarily fasten the plate with one steel nail. 2.
3.Installation of the Indoor Unit Drawing of pipe Rear piping Draw pipes and the drain hose, then fasten them with the adhesive tape Left Left-rear piping In case of left side piping, cut away, with a nipper, the lid for left piping. In case of left-rear piping, bend the pipes according to the piping direction to the mark of hole for left-rear piping which is marked on heat insulation materials.
Indoor unit When connecting the cable after installing the indoor unit 1. Insert from outside the room cable into left side of the wall hole, in which the pipe has already existed. 2. Pull out the cable on the front side, and connect the cable making a loo p. When connecting the cable before installing the indoor unit Insert the cable from the back side of the unit, then pull it out on the front side.
20 g/m. But the charge of refrigerant must be conducted by professional air conditioner engineer. Before adding additional refrigerant, perform air purging from the refrigerant pipes and indoor unit using a vacuum pump,then charge additional refrigerant.
After attaching the each caps, check the gas leakage around the caps. CAUTION: 1.If the refrigerant of the air conditioner leaks, it is necessary to discharge all the refrigerant. Vacuumize first, then charge the liquid refrigerant into air conditioner according to the amount marked on the name plate.
1.Power Source Installation The power source must be exclusively used for air conditioner. (Over I0A) In the case of installing an air conditioner in a moist place, please install an earth leakage breaker. For installation in other places, use a circuit breaker as far as possible.
Haier Industrial Park, No.1 Haier Road, Qingdao, P.R.China CONFORMITÀ ALLE DIRETTIVE EUROPEE PER I MODELLI: Tutti i prodotti sono conformi alle seguenti normative europee: - Direttiva 73/23/EEC Basso Voltaggio - Direttiva 2006/95/EC Basso Voltaggio - Direttiva 89/336/EEC Compatibilità elettromagnetica - Direttiva 2004/108/EC Compatibilità elettromagnetica ROHS Il prodotto è...
Haier Industrial Park, No.1 Haier Road, Qingdao, P.R.China CONFORMIDAD EUROPEA DE LAS REGULACIONES PARA LOS MODELOS: Todos los productos están en conformidad con las siguientes Normativas Europeas: - Bajo Voltaje directiva 73/23/EEC - Bajo Voltaje directiva 2006/95/EC - Compatibilidad electromagnética 89/336/EEC - Compatibilidad electromagnética 2004/108/EC...
Haier Industrial Park, No.1 Haier Road, Qingdao, P.R.China Contains fluorinated greenhouse gases covered by the Kyoto Protocol R410A INFORMAZIONI IMPORTANTI SUL REFRIGERANTE UTILIZZATO Questo prodotto contiene gas fluorurati ad effetto serra inclusi nel Protocollo di Kyoto. Non liberare tali gas nell’atmosfera.
Haier Industrial Park, No.1 Haier Road, Qingdao, P.R.China Contains fluorinated greenhouse gases covered by the Kyoto Protocol R410A INFORMACIÓN IMPORTANTE EN RELACIÓN AL REFRIGERANTE UTILIZADO Este producto contiene los gases fluorados de efecto invernadora regulados por el Protocolo de Kioto. No vierta gases a la atmósfera.