All manuals and user guides at all-guides.com NOTICE Before you install the devices, closely read the SUN2000 (8KTL-28KTL) User Manual to get familiar with product information and precautions. To locate the user manual, log in to http://support.huawei.com/carrier/ and browse or search for SUN2000 on the Product Support page.
Mount the inverter on the rear panel. M10 (3 PCS) 30 N· m Tighten hexagon bolts. (Optional) Install an anti-theft lock. NOTE The antitheft lock is prepared by customers. For details about wall-mounting the device, see the SUN2000 (8KTL-28KTL) User Manual.
The table lists only the recommended cable specifications. For more information about cable specifications, see the SUN2000 (8KTL-28KTL) User Manual. NOTICE Do not use solid conductor hard cables. 3-core outdoor cables (L1, L2, L3) are configured for the SUN2000-28KTL and 4-core outdoor cables (L1, L2, L3, and N) are for other models.
All manuals and user guides at all-guides.com sealing Cable Socket cover Large handle Auxiliary screwdriver connector (recommended) NOTICE The N cable is inserted into hole 4. Do not insert L1/L2/L3 into Click Notch NOTE To quickly connect the AC output connector to the AC output terminal of the inverter, keep the notch of the connector facing exactly to the operator.
All manuals and user guides at all-guides.com Positive and negative metal terminals: Positive metal terminal (female) Negative metal terminal (male) Positive metal terminals Recommended: H4TC0001 (Amphenol) Negative metal terminals Ensure that cables cannot Common PV cables with a cross- sectional area of 4 mm² in the be removed after crimped.
The preset password for Common User, Advanced User, and Special User is 000001. Use the preset password to log in to the SUN2000 for the first time and then change the password to a new one to ensure the account security.
All manuals and user guides at all-guides.com Main Second- Third-Level Fourth-Level Menu Setting Menu Level Menu Menu Wizard Language Set based on site requirements. Date&Time Date Set based on site requirements. Time Set based on site requirements. China medium-voltage power grid, Grid Code choose CHINA-MV480.
All manuals and user guides at all-guides.com Appendix: Power Grid Standard Code Mapping Table Power Grid Power Grid Country and Condition Country and Condition Standard Code Standard Code China medium-voltage IEC61727- IEC medium-voltage power CHINA-MV480 power grid MV480 grid China low-voltage power VDE 0126-1-1- Bulgaria low-voltage power NB/T 32004...
All manuals and user guides at all-guides.com HUAWEI TECHNOLOGIES CO., LTD. Huawei Industrial Base Bantian Longgang Shenzhen 518129 People's Republic of China www.huawei.com...